Nate and Patrick were efficient, polite and prompt. We would definitely recommend Cool Air Solutions based on their work.
Jimmy was great. Very knowledgeable and friendly.
The technician took extensive time to check the whole system, including the A/C unit, explaining what needs to be done in the future.
Upon arrival found thermostat to be faulty. Does not engage for heating, replaced under warranty and installed a honey well T6 pro WiFi, replaced filter. System is operational upon departure.
Arrived on site to diagnose a air flow issues on a 2019 good and system. 2019 Condenser in back yard. 2000 furnace and 2019 evaporator coil located in garage. Spoke to client about issue a a she stated she feel system is not producing enough air flow to master and would like to see what can be done to provide more air flow to master bed room. As well there is a noise being made when ever blower is operating. Found due to age of system and itâ€™s condition blower assembly now has some play on assembly as it has creates a bit of vibration When operating. She cycled system on cooling. Both units operating. Inspect attic and duct. All good. Inspected furnace. Found filter dirty and in need of replacing. Recommend doing more frequently to reduce the amount of dirt entering system. found blower motor has been leaking oil in past as dirt and oil are building up. Blower wheel is heavily dirt from lack of filter change out. Creating high stress on blower motor and making it work harder due to
Replace existing system with listed equipment. Seal return platform, install new Merv 11 5â€ filtration system, install new condensate pump under platform, seal and install new high flow register set and seal cans. permits and HERS included
Performed AC maintenance
Also includes Merv 16 filter promo on both units
A.c. maintenance in Spring Valley
Sdge quality maintenance on Weather King equipment
Furnace maintenance and filter replacement in Spring Valley
Air conditioner tune up
Performed routine air conditioning maintenance on lennox unit in spring valley
Air conditioning maintenance and coil cleaning in La Presa San Diego.
Upsizing duct work supply to upstairs to get more airflow to the bedrooms, also upsizing return to make equipment quieter and more efficiant.