Preformed condensation line repair. Client stated that secondary has been draining out the side for a couple of days now. Inspected drain lines in the attic and found that the primary Is indeed blocked up. Preformed cut and clear on drain lines, ran dry nitrogen to clear ant debris. Primed drain line to confirm proper drainage. If leakage continue can also be related to crack evap coil pan. Upon departure system is draining out of primary.