Maintenance performed on Goodman system. Checked ampâ€™s of blower motor and furnace itself, system using low amps. The filter was still clean and can be replaced next maintenance visit. The temperature split was in range to heat home properly. Coil is clean, and gas line is in open position. Turned heating off and checked through all electrical components. All components operating correctly. System is operational upon departure. Moved onto Lennox mini split and set in heating mode. Cleaned out air filters inside mini split head. Checked voltage tightened electrical. Noticed the condenser was dirty so I went ahead and cleaned off unit. System heats well, and operational upon departure.