Tech arrived on site. Found the capacitor to be leaking oil and completely failed. Replaced capacitor and found the compressor to be over amping. Also the return is undersized. Client said the room closets to the garage is always hot. Recommend adding a return into the room. Clients are considering replacing the unit do to age and condition. Also possibly adding a mini split in the garage.