Performed AC diagnostic on 18-year-old Aireflo Condensers. Upon my diagnostic client initially stated that just the other day the condenser fan motor had failed and is no spinning. Performed full diagnostic on system and found multiple points of concerns. 1. Outdoor condensing fan motor has completely failed and is no longer spinning due to it locking up. 2. Starter showed signs of pitting and burn marks on contact points 3. System Contained R22 refrigerant which was completely phased out on January 1 2020. 4. Condenser had a coil Rot 5. Compressor saver kit should be installed to help reduce start up amps 6. Service disconnect was not equipped Surge protection or fuses. Discussed full condition of system with homeowners and they would like to replace everything. No repair was done at the moment and will be returning for a full system installed.