Five stars He was nice and worked the entire time he was here.
Sam is a great technician. Very friendly and explained what the issue was so I understood it. I appreciated that he gave me the full options and didn’t try to pressure me in the most expensive option. I really like having Sam come because I feel that he is being honest with me.
Cool Breeze was quick to respond when our heat went out. Sam came out first thing the next morning, was quick to diagnose the issue and repair it. Sam was very professional and explained the issue in detail.
We had them install a York heating & air system last summer, which is working great. Sam came out this morning to help me find the damper adjustment for winter, and was professional, courteous and helpful. Highly recommended, thank you!
After hours service provided, solved our AC problem and thankful we can sleep in a cool house tonight! 😎
Did a great job, was knowledgeable and friendly.
I could not have asked for better service. Everything was explained to me in detail before any work was performed. Before I knew it my house was at a comfortable temperature again. I can't thank you enough!
Had a great experience and will definitely use again and recommend
Came out late at night. AC is working again.
York affinity spring check up. No issues found.
Trane heat pump low on r22 refrigerant.
Resistance on grounded compressor , goodman heat pump service call
Inspection for house sale hvac Rudd 80% natural gas Quiet80 from 2005
Comfortmaker 10 seer heat pump spring tune up with coil cleaning
Carrier 2005 spring tune up. Found low on Freon.
Don’t know what brand this is spring tune up
Duct pressure test for leaking ductwork
Keep your Trane heat pump running forever. Get a tune up twice a year.
Compressor change out on a carrier heat pump
3 Trane units ready for spring tune up, clean with chemical cleaner and test operations
Blue ridge heat pump new install, top off with 410a refrigerant.
Goodman r22 unit low on charge, freezing up
Carrier straight AC spring tune up
Payne heat pump clogged drain line