plumber recognized Sewage blockage could be on public utility line rather than private home line. Utility looked at problem, agreed it was their problem to fix. Utility asked that your bill be sent to them to be paid.
I would definitely use Tony and CPI again!
I set up the man lift underneath the already removed ceiling tiles. I shut off the cold water valve that was installed during the previous repair. I cut out the failed cold copper water supply. I provided and installed new copper tubing and fittings. I turned the water back on and tested the repairs. Everything is in great working condition at this. * CPI is not responsible for any damages or repairs made to the drop ceiling or walls.
In the womenâ€™s bathroom the last toilet in the line which is the ADA stall the toilet was clogged. I tested the other toilets in the bathroom and in the menâ€™s bathroom to see if it was possibly a mainline issue or if it is isolated to that one toilet. After running my test I found it to be isolated to that single toilet. I got approval to begin work so I pulled my toilet auger off of my truck and set up in front of the toilet and began to auger down through the bowl. I hit something in the upper end of the trap and as the head of my snake hit it the clogged released and passed through the system. I tested the toilet several times to make sure there was no more of a blockage. I then tested each one of the other toilet to make sure it didnâ€™t cause a mainline blockage. Both bathrooms are up and running. There is no warranty or guarantee on drain cleaning.
Arrived on site due to customer request of getting his heating system looked at. Customer does not have enough wires to run a duel fuel system. We recommend installing a Honeywell Pro 9000 thermostat with an EIM to limit the needed wires and adding an outdoor wireless thermostat for proper duel fuel operation. Provided customer pricing for a new heat pump system. Insured the unit was working properly upon leaving. Thank you for choosing CPI Plumbing & Heating Inc.
We pulled the downstairs toilet to try and determine if the water that is coming up through the grout lines between the tile on the floor is either from the toilet leaking from around the wax ring or if its from another source. When the toilet was removed we found small dirt piles that built up and ground water coming up trough the hole in the concrete that the toilets flange is located. There is no way to seal up the space between the ABS pipe and the concrete that it comes up through. The ground water around the foundation needs to have a way to move away from the concrete.
Performed hand excavation to expose side sewer piping to find leak Removed cherry tree with ownerâ€™s consent Found break in orangeburg sewer piping Strongly recommend replacement of all orangeburg sewer piping as there are other areas with damage and root intrusion Orangeburg piping runs from abs (black piping cleanout in backyard to white pvc cleanout in neighboring yard Recommend contacting city to see about providing sewer stub onto eproperty this would have to be coordinated for proper depth Will provide owner for side sewer replacement approximately 30 to pvc ewezs$eedseszessseznear street Repair has been bedded in pea gravel Running water test (no leaks visible) had owner run and flush multiple fixtures No warranty on any existing plumbing
The dishwasher that I installed was not lining up with the cabinet. I removed the screws and set the dishwasher back. Dishwasher is now set and approved Mrs.Ryan.
Kitchen I removed the existing disposal, emergency shut off valves, and all waste piping. I rerouted the water lines and supported them in the wall. I installed a new drain line and clean out for the kitchen sink. Range I removed the valve and gas line for the rang. I capped the 1/2 inch gas line at the main trunk line. Crawl space I cut out the old ice make line and repair the existing copper tubing. I turned the water back on and tested the repairs. Everything is in great working condition at this time.
Removed a whole bunch of routes from inside the storm drain. Could not get the camera through the drain line due to the amount of routes. Was able to blast the dirt out of the pipe which now allows it to drain and keep up with the gutters. I recommend that when the rain stops that a hose get placed down the drain line and turned on then looking for the water to come out next to the creek in the backyard to find the exit of the pipe.
Checked customer complaint about sewage running into their and their neighbors yard. Customer told me sewage has been backing up out of the ground for a few days. Checked main drain line through outside clean out and discovered the line was backed up. Offered pricing to augur out the drain line which included a camera inspection. After pricing was approved I performed auguring of main drain line. I laid down a rug to protect the customers lawn and hand fed the cable into he line until I hit the obstruction. I hit the obstruction about 15 feet into he pipe. After obstruction was found I power fed the cable to work through the obstruction. I was able to clear the obstruction and the pipe drained. I power fed the cable to the main to ensure that the obstruction didnâ€™t get stuck down the line. I removed the cable from the line. Performed Camera inspection of the main drain line. Discovered about 10 feet into the pipe that There was a big hole in the pipe where the sewage was exiting. Off
Everything in the home is backing up into the bath tub even when no plumbing is being used in the home. I pulled the toilet and discovered that the flange was broken and the drain line was full of water. I ran the camera down the drain and discovered that the line was backed up over 100 feet. I spoke with Kevin on the phone and he informed me that the city was working on the drain lines last week and that some of the other units had drains backing up. Last week was when everything started backing. I repaired the flange and reset the toilet. The floor around the toilet has water damage and should be looked at. I spoke with Kevin again and he contacted the city and will have them inspect the situation. * Further charges will apply for any further diagnostics or drain cleaning. * Kevin mentioned that the park drain lines are 10â€. * No warranty or guarantee on the plumbing system.
I cleared the first menâ€™s room urinal in the customer bathroom. The urinal is now flushing as designed. * No warranty or guarantee on drain cleaning. * Further charges will apply if urinal backs up again.
Provided pricing options per customers request
Heat pump is low on refrigerant and may be damaged. Customer has asked for pricing to abandon it and remove it and to rewire the thermostat to ignore the heat pump entirely. Arrived onsite. Isolated power to outdoor unit. Removed 240 volt whip to outdoor unit. Shut disconnect door and zip tied the lock slot. Recovered refrigerant into outdoor unit. Cut line set and removed it. Left 6 inch stub of Lineset at the coil, brazed the ends of the stubs shut. Rewired airhandler. Rewired thermostat. Confirmed operation of the airhandler. 100 degree supply air to the home. 65 degree return air. Outdoor temp is roughly 40 degrees. Thank you for choosing CPI Plumbing and Heating Inc.
I installed an owner supplied pot filler, dishwasher, kitchen faucet, and disposal. I provided and installed a new emergency shut off valve and ran a new water supply for the new pot filler. I tested all the installations and everything is in great working condition at this time. * No warranty or guarantee on owner supplied fixtures.
Arrived onsite customer was complaining of a strange noise. Large piece of cardboard was blocking return air plenum once moved noise went away. Customer will sign up for a membership to get her furnaces serviced once her filter needs to be replaced. Thank you for choosing CPI Plumbing and Heating Inc.