plumber recognized Sewage blockage could be on public utility line rather than private home line. Utility looked at problem, agreed it was their problem to fix. Utility asked that your bill be sent to them to be paid.
I would definitely use Tony and CPI again!
10/26/2020 Confirmed with customer that mainline is backed up. Outside clean out is empty not backed up so determined that blockage is between drain line exiting building and outside clean out. Will need to camera line to verify cause of blockage. Gave customer estimate to inspect drain line. Thank you for choosing CPI Plumbing and Heating.
Arrived on site to perform annual safety and maintenance inspection. Began by testing my inlet gas pressure which gave me a reading of 6.60. Tested my flame sensor and gave me a rating of 2.2 ÂµF. Tested my inducer and was pulling .54A. Bower was pulling 1.89A. Measured for my Delta T and got an air temp differential of 25Â°. Tested for CO inside home found none. Changed 14 x 20 x 1 air filter. Insured everything was working properly upon leaving. Thank you for choosing CPI plumbing and heating Inc.
Arrived on site per customer request of getting a new venting system made up for a 1200 CFM Kitchen Range. Upon arriving we discussed the situation with Jennifer and made her aware of the necessary components involved with running such a big fan. CPI will be running a new venting system through the roof for the kitchen range. Todayâ€™s work involved us installing a new fresh air makeup with a damper that attaches to the return air duct. CPI will be installing the venting for the kitchen range once the appliance guys set the range as well as the blower on the roof. Jennifer will be calling to schedule us out once she finds out when the appliance guys will be coming. Note: CPI is not responsible for hooking up the electrical for the damper, an electrician will be needed to power up the transformer. Thank you for choosing CPI plumbing and heating Inc.
Changed out the guts and all of the trim kit for both of the tub shower combination units from chrome fixtures with plastic candles to brush nickel with metal handles. Turn off the water to the house and cut into the 1 inch copper mainline soldered 1 inch packs adapters and ran 1 inch along the crawlspace ceiling over to the laundry sink where I drilled holes that the new 1 inch main shut off ran up through and back down. Now the whole house main shut off is located under the laundry sink. At the kitchen sink removed the faucet and the three hole cover plate in the far left hall installed a dishwasher airgap and ran new piping to connect airgap to the garbage disposal. Underneath the pedestal in the guest bath installed a new tubular P-trap and replaced the cold angle stop that was leaking as well as the supply line. Under the kitchen sink replaced the cold angle stop with a new double emergency stop and connected the new quarter inch braided steel flex supply that was routed through t
Customer called in with a broken kitchen faucet, and a running toilet. Arrived on site and inspected the issue. The toilet in the upper apartment unit is running, and the shut off valve does not work, the kitchen sink faucet is loose and the mounting hardware is rusted. Provided pricing to perform a minor rebuild on the toilet, install a new quarter turn emergency shut off valve, and to replace the kitchen faucet. The customer accepted the pricing. Shut water off to the unit, removed the existing toilet shut off valve, installed a new quarter turn emergency shut off valve, installed a new fill valve, flapper, and supply line for the existing toilet. Restored water to the unit, bled air from the system, and tested the toilet. The toilet is no longer running and is working as designed. Removed the existing kitchen faucet. Installed a new Kohler faucet. Tested the new faucet. The new faucet is working as designed. The dishwasher air gap was installed in the furthest hole away fro
Arrived on site. Provided and installed new pop up assembly in upstairs bathroom. Shut down water to the home and drained water through outdoor hose bib. Provided and installed two new 1/4 turn angle stops in upstairs bathroom. Restored water to the home and checked for leaks. No leaks were identified. Bled the remaining air from the lines and ensured fixtures were operating correctly. Everything is in great working condition at this time.
Started day one of remodel. Provided and installed new ice maker box and main water shutoff valve located in the hallway closet. Repipe sections of water piping in crawl space. Provided and installed new quarter turn emergency shut off valves for the kitchen sink. Turned water on and tested for leaks. No leaks were detected. Everything is in good working condition at this time.
Perform inspection and serviced water heater. Provided estimate on repairs Emailed estimate on repairs to customer. Thank you for choosing CPI!
Dishwasher washer technician stated that the incoming water was not hot enough for the commercial dishwasher and needed to be 140 degrees. I tested the incoming water multiple times and each time the temperature was between 140-150 degrees.
Arrived onsite customer wanted his furnace inspected. Furnace was 29 years old so I provided pricing for a replacement. Overall the measurements I took on the components were where they should be. Unit was clean as it was cleaned and serviced back in 2019. Customer also had a hosebib that was leaking from the packing nut. Attempted to tighten the packing nut, packing nut would not tighten. provided pricing for a new hosebib and will look into the possibility of replacing the packing nut. Inspection form on the furnace will be emailed to the customer. Thank you for choosing CPI Plumbing and Heating Inc.
We use the outside clean out for the point of entry to unclog the main line. Once we had the drain completely clear and running we ran the camera down the drain line and located a route intrusion on the backside of the house. Advised him to not use any items down the drain line that could possibly get caught in the roots will have to get pricing put together to dig up and remove the roots from the system. After a little bit of questioning with the neighbors we found that the line that has the roots is actually a trunk line and not a branch and is part of the main sewer for all the neighbors.
Disconnect and remove existing pump. Install new Gouldâ€™s pump. Perform connections to suction side of pump and discharge side of pump with 2 unions and brass fittings. Install new pressure switch and boiler drain on tank tee. Perform wiring connections to new pump and new pressure switch. Turn power on to pump. Purge air out of suction side of pump from the lake. 2 year warranty on new pump installation. Thank you for choosing CPI
Performed repair on leaking lav drain in master bathroom tested no leaks (no charge on repair) 11:00-12:00 pressure test on both sinks in master bathroom Diagnostic on steam unit, unit takes a few minutes to heat and produces steam settings range from 2-20 min left manual on counter top Performed diagnostic on lav faucet, dismantled pulled aerator no debri present reassembled as a courtesy sealed beauty plate on hot side handle west sink in master bathroom Performed full floor and surround caulking seal on mop sink recommend 24 hour cure time before use
Customer called in for emergency after hours service for no hot water. Arrived on site and inspected the issue. The hot water heater is a Bradford white Propane unit, the tank is 7 years old. Provided pricing to perform a plumbing diagnostic which the customer approved. I was on site at this location recently for a separate issue. While there the neighbor had been helping the customer and may have shut a gas valve off causing the water heater to lose its pilot. There has also been heavy wind in this area due to a recent storm which could have affected the pilot. Attempted to light the water heater pilot. The pilot immediately lit. Turned the gas control valve to the operating position. The tank fired up as designed. The flame is healthy and consistent. The customer now has hot water. Showed the customer how to light the pilot properly in the event that it goes out again. Thank you for choosing CPI Plumbing & Heating!
Customer request for new 50 gallon natural gas water heater. Gave option to install new 50 gallon Bradford white natural gas water heater. Turned off incoming water at the meter. Removed existing water heater from closet. Installed new 3/4 ball valve. Installed new earthquake strapping. Installed new 50 gallon natural gas water heater with new flex supply lines and gas supply line. Once I had all my connections made I then went to turn the water back on to test for leaks. No leaks were detected at this time. I then opened up the valve and began to fill the tank. Once the tank was full I then fired off the tank, informed the customer that it would about 45 minutes for hot water. Double checked all my connections for leaks. No leaks at this time. Cleaned up work area. Thank you for choosing CPI plumbing and heating.