Great job thanks
Everything was well done. Great people.
Coady did a great job. Water is back up and running.
Replace Inducer Motor 11-30-22 arrived and provided and installed new inducer motor housing, gasket, and wiring. Once unit was properly installed. Turned shop heater on and set thermostat to 60 and unit fired off. Checked for CO and measured none. Talked with Dylan about what temperature to leave thermostat set to. He had stated 85 would be nice I informed Dylan that 85 is extremely hot and I would recommend leaving it at 60 . The building is a tin pole shop with little to no insulation. Unit heated from 39 degrees to 48 degrees in the course of the time spent on job. No CO was measured. CPI strongly recommends having chimney cap on exhaust piping to prevent rodents or birds from entering system and having working CO detectors in shop. Replace Inducer Motor
Arrived onsite and ran gold membership Cleaned fins on exterior of heat pump and wiped excess algae and grass away from unit. Checked current draws on compressor and outdoor fan motor. Outdoor unit appears to be functioning well. Ran heating system through cooling and heating and found both temperature splits to be within tolerance. Ran system through emergency back up heat and had a temperature split of approximately 50F with no CO. This temperature split seemed high. Checked filter and found filter to be completely saturated. This is believed to have caused the high differences in temperature across the heat exchanger. Blower and inducer motor appear to be pulling good current within appropriate tolerance. Air scrubbed bulb is believed to be burn out. Voltage is present to the air scrubber but operation light is not on. Customer had stated that she runs the fan setting to ON to circulate air through system. This is believed to have burnt bulb out. CPI recommends re
Customer called in because of stoppage in her mainline. Inspected crawlspace and found that San Tee was on its back.. Customer had side sewer exposed and cut out. Ran camer towards home and found that stoppage was in fact on San tee. When camera hit obstruction the blockage dislodged and sewer became free flowing. Ran camera through rest of line and found that there was a separation on line at approximately 55feet. Approximately 5feet down. Gave pricing to customer for replacement of drains throughout home as portions of drains were back graded and there had been abs piping glued into PVC fittings. Note: notified customer that additional pricing may need to be presented in order to provide proper venting for drain system. Will send out pricing for customer by next Wednesday for replacement of side sewer. Thank you for choosing CPI and heating!
Performed work as proposed. The customer wanted to have an ice maker box installed. I laid down a rug to protect the customer’s floor from damage. We cut out the existing pinhole valve and capped off that part of the line. Performed installation of the new ice maker box. The new ice maker box was installed with a braided stainless steel supply. After the ice maker box was installed I had the customer turn on the water and we tested for leaks with the customer. The ice maker box performed as designed and there were no leaks when last checked. The customer was happy with the new ice maker box. CPI is not responsible for drywall patch and repair. The customer understood They are fully responsible for drywall patch and repair. Thank you for choosing CPI Plumbing and Heating.
Checked customer complaint about a possible leak in the crawl space. The customer believed he had a leak in the crawl space from the ice maker line. Presented customer pricing to perform a leak search. After pricing was approved I went into the crawl space and did not find any signs of a leak. The customer decided he wanted to install an ice maker box. Presented customer pricing to install a new ice maker box. After pricing was approved I took a half down deposit. The customer had an appointment so the work was rescheduled for Tuesday September 6th. Will return to perform work on scheduled day. Thank you for choosing CPI Plumbing and Heating.
Arrived at KOA Started to perform work proposed Started to excavate Upon excavating we noticed a wye fitting with corrugated pipe taped to it Notified customer that he will have to call a septic company to do the necessary repairs Customer acknowledged and agreed Customer would also like to have backflow preventer installed another day as he wants to give notice to campers and time to drain Notified customer that we can come out on Wednesday the 24th Customer acknowledged and agreed that time would work Thank you for choosing CPI Plumbing and Heating
Arrived at KOA Customer stated that they have a broken septic line Gave customer pricing to perform diagnostic Customer agreed to pricing Started to perform work proposed After checking septic tank we noticed that is is completely full Notified customer that they will have to empty tank out before we can dig Customer stated that they will call septic company and then will call us back to reschedule Notified customer that while we were there that we had seen a backflow preventer that is leaking and would give pricing for that as well Customer acknowledged and agreed Thank you for choosing CPI Plumbing and Heating
Completed Rough in plumbing as proposed. Tested water at working pressure. Performed stack test on waste and vent piping system.
Performed work as proposed. I cit our the damaged section of pipe and installed the new section of pipe. After the new section of pipe was installed and secured I ran large quantities of water down the drain to test for leaks and drainage. The new section of pipe performed as designed and there were no leaks when last checked. Performed plumbing safety and maintenance inspection. I began inspection by checking incoming water pressure and peak water temperature. The water pressure was at 60psi and the temperature was at 120 degrees. Performed water heater inspection. All components of the water heater performed as designed. Performed the inspection of all plumbing fixtures in the home. All plumbing fixtures in the home performed as designed. Performed crawl space inspection. All plumbing in the craw space were free of any damage or deformities and were properly installed. The customer was happy the pipe was repaired and all plumbing fixtures performed as designed. Thank you for choos
Customer stated water heater was leaking. Found water heater to be leaking out of control valve. Provided estimate to replace water heater and customer agreed to work. Turned off water and gas to water heater. Drained water out of tank. Removed old water heater. Installed new 50 gallon Propane water heater and new water heater stand. Installed earthquake straps. Filled tank with water and verified no leaks present. Turned on gas to water heater and used gas sniffer verifying no gas leaks. Set water heater temperature to 120 degrees. Thank you for choosing CPI plumbing and Heating.
Site 80= leaking gate valve Between cabin 5-6 leaking hydrant Site 8= leaking hydrant 4” leaking gate valve Arrived onsite to customer complaint of a furnace not working and some yard hydrants needing to be replaced. Yard hydrants are leaking at the base. Two gate valves are also leaking, working on pricing for these repairs. Customer stated that they will dig up all four areas with issues and we can come perform repairs. Contacted Amanda the park manager, who approved thermostat replacement, furnace diagnostic and dispatch fee, over recorded phone line. Performed diagnostic, found a bad inducer motor. Replaced thermostat and set in an area with easier access. Sent pricing for inducer motor replacement Amanda will have to approve pricing and pay half down before the inducer motor is ordered. Thank you for choosing CPI Plumbing and Heating Inc.
Customer called in wanting a filter replacement, and had a issue with water pressure surging. Performed replacement of pre and post filter. Went over installation with customer and demonstrated how to perform replacement of each filter. Performed isolation of pressure tank and checked PSI. No PSI was present. Replacement of pressure tank was recommended. Customer decided to move forward with replacement at this time. Drained down pressure tank. Removed tank tee. Removed section of existing copper piping. Cut away existing isolation valve. Installed new tank. Installed new tank tee. Installed new pressure switch. Returned water to system. Checked for leaks. One of the filter housings had a small weep present. Isolated housing. Performed drain down. Replacement existing o ring. Reinstalled. Returned water to system. Checked for leaks again. No leaks found at this time. Thank you for choosing CPI plumbing and heating!
Checked customer complaint about a clogged main line. The customers main to the septic was clogged but cleared itself and he wanted a camera inspection. The customer also needed the under sink waste pipes under his kitchen sink replaced. Presented customer pricing to replace the under sink waste pipes and perform a camera inspection. After pricing was approved I laid down a rug to protect he customer’s floor from damage. I removed the existing under sink waste and basket strainers and installed the new ones. Performed leak test on the new under sink waste pipes. The drain performed as designed and there were no leaks when last checked. Performed camera inspection. When I performed the camera inspection from the outside clean out to the inside of the home I discovered standing water in the first ten feet. I went into the crawl space and discovered the line was not properly secure 10 feet before exiting the foundation. I readjusted the anchors and restored the pipe to the proper grade. T
Customer called about a leak underneath their guest bathroom lavatory sink. Upon arrival, found leak to be occurring at the cold water line connection at the faucet. Neither water supply had a shut-off valve. Water piping is qwest going straight to the faucet. This water piping is not approved to be installed within the home. Offered pricing to install a new shut-off and supply line on the cold side but also offered to install two shut-off valves and supply lines on both water lines. Customer agreed to the estimate for two new valves and supplies. Powered off water heater, isolated water supply, drained system. Cut out about 2’ of each qwest water line and installed two new quarter turn ball valves with new supplies and push fittings. Turned water back on, purged air. No leaks detected, ball valves working as intended. Powered up water heater. Cleaned work area. Thank you for choosing CPI!
Customer called in because of mainline stoppage at two different sites. A campsite and the mainline right before the septic. Ran drain inspection equipment down cleanout and found stoppage at approximately 50 foot. Ran drain cleaning equipment to approximately 60 feet. Saw and hear water drain. Ran camera down and found standing water still inside of piping. Removed septic lids and saw water above secondary baffle. Removed baffle filter and witnessed water start to drain. Cleaned off baffle filter and reinstalled. Line is clear but approximately 5-10 feet before baffle standing water is still present inside of piping. Ran drain cleaning equipment down secondary cleanout at campsite. Found standing water inside of pipe. At multiple places. No signs of stoppage found. More drain inspection work required. CPI plumbing and heating does not warranty or guarantee any drain cleaning. Thank you for choosing CPI plumbing and heating!