Not only did I save money, but I received fast service from knowledgeable people. I called another company that I had used before and they made me wait 2 hours before telling me they couldn't help me. So when I called Crystal Blue and spoke to someone right away I was impressed. I will use them for everything in the future.
I have had 3 technician's out to my home thus far and each one was courteous, efficient and so friendly. It's been a long time since I have received service on this level.
Our AC unit went out when it was 104 degrees. Jordan was out the next day hours early and had us up and running in 10 minutes!
Michael, provided OUTSTANDING service, his customer rapport is truly professional. He responded in a timely manner with consideration to our time and was extremely courteous. A customer oriented technician of the highest caliber. mm
Great communication great customer service and fast install
friendly and good service
Called customer and they cancelled.
Performed ac maintenance on electric roof top package unit. Went thru system first for heater to warm up house, cooler morning... then tested ac. System is from 1977. It is working for now just not running as good or efficient as it could be. Blower has a slight wiggle and vibration. All parts are working for now. Due to age of system want to watch how much money you put into system for return on investment. Change filter more often. Electrical connections ok at this time. Refrigerant ok at this time.
Performed annual heat maintenance on Lennox electric package unit roof. Unit is original from 1977. 42 yrs old. Went thru and unit is showing its age, blower is dirty, blower is also vibrating. Changed filter, in pretty roof shape recommend replacing filter more often. System running, just not as effiecntly as.
Provided plumbing maintenance water heater is from 1999 flushed water heater and inspected all plumbing fixtures throughout the house. Going to provide a estimate for water heater replacement.
Left estimate to install a puronic whole house water conditioning system, this unit will remove all the calcium and magnesium from the water with very minimal sodium use it also removes the chlorine from the water and the sand sediment dirt and debris has a limited lifetime warranty through the manufacture.
#no No estimate given. Will revisit in October when homeowner is ready to move forward.
Antelope ca. Remove old kitchen faucet and install new kohler faucet with side spray. Tested and found no leaks. I do also recommend to replace the garbage disposal due to age and stress cracks#no. unable to get to the rest of the home due to the dogs in the house, homeowners would like one of our heating and air specialist to come out and give them an estimate on a new unit. Unfortunately I have no info on the unit due to not being able to access it
Performed ac diagnostic, 16 yr old hydronics unit in upstairs bathroom ceiling and out back. system trying to turn on, outside has a bad dual capacitor. Replaced part and tested system. Client to call in credit card in 30 mins
Client called and cancelled yesterday per ken.
There is currently a leak underground in the main water supply that has been temporarily rerouted above ground using a hose, the PVC pipe looks to be going directly under a palm tree , I cannot tell where the line is broken unless we do a leak detection. this is special equipment used to locate leaks below surface. the leak could be under the palm tree and the only way to repair that leak is remove the palm tree or reroute the line. Homeowner is currently in talks with the original companies that had dug in the area and has also had estimates from other plumbing companies. Unfortunately without doing the leak detection I cannot tell wear the pipe is broken.
Performed ac maintenance antelope, 27 yrs Goodman split system garage back yard. Found filter dirty and in upside down, recommend replacing more frequently. Client changed return grill, and wants to put filter there and remove filter inside blower compartment. Blower capacitor out of range still low. firstname.lastname@example.org. Blower dirty, see pictures. Evap coil doesnâ€™t have a secondary drain line just overflows onto unit. Condenser dirty coils on back side of unit especially bad. Washed unit. Top of unit still cracked. Compressor start capacitor email@example.com low. System appears to be low on r22 refrigerant see pressures, just below the freezing point. But with everything else going on wonâ€™t know for sure until all recommended repairs competed. With age of system and shape of system, recommend repair vs replace options. Went through entire ac system, cleaned and checked all parts.
Added new 16â€ return to living room wall. Increased the hard pipe return in garage from 16â€ to 18â€. Installed adjustable 18â€ 90 through ceiling in garage and 18x16x16 wye in attic to attach the new and old returns. Installed high flow return grille at new return location. Found 4â€ supply at bathroom disconnected and reconnected it. System is now running with much better airflow and is no longer restricted.
Add 2nd return to system to improve airflow to system and to extend life of unit. Current return undersized for unit and home. Would need to enlarge 16â€ duct to an 18â€ duct. And adding an 18â€ adjustable 90, as well as a 18-16-16 wye. Then connect the old 16â€ duct and a new 16â€ duct as well as 14-30 return filter grill and can. 650 original bid 572 Total 1222$ Emailed new estiment to client
Homeowner getting other estimates
Roseville California AC heating service AC heating maintenance AC heating diagnostic furnace not coming on not producing heat. found problem to be a plugged pressure switch port. cleaned pressure switch port and inducer assembly to help prevent pressure switch port from getting plugged by debris