Not only did I save money, but I received fast service from knowledgeable people. I called another company that I had used before and they made me wait 2 hours before telling me they couldn't help me. So when I called Crystal Blue and spoke to someone right away I was impressed. I will use them for everything in the future.
I have had 3 technician's out to my home thus far and each one was courteous, efficient and so friendly. It's been a long time since I have received service on this level.
Our AC unit went out when it was 104 degrees. Jordan was out the next day hours early and had us up and running in 10 minutes!
Michael, provided OUTSTANDING service, his customer rapport is truly professional. He responded in a timely manner with consideration to our time and was extremely courteous. A customer oriented technician of the highest caliber. mm
Great communication great customer service and fast install
friendly and good service
Performed ac diagnostic, 16 yr old hydronics unit in upstairs bathroom ceiling and out back. system trying to turn on, outside has a bad dual capacitor. Replaced part and tested system. Client to call in credit card in 30 mins
Client called and cancelled yesterday per ken.
There is currently a leak underground in the main water supply that has been temporarily rerouted above ground using a hose, the PVC pipe looks to be going directly under a palm tree , I cannot tell where the line is broken unless we do a leak detection. this is special equipment used to locate leaks below surface. the leak could be under the palm tree and the only way to repair that leak is remove the palm tree or reroute the line. Homeowner is currently in talks with the original companies that had dug in the area and has also had estimates from other plumbing companies. Unfortunately without doing the leak detection I cannot tell wear the pipe is broken.
Performed ac maintenance antelope, 27 yrs Goodman split system garage back yard. Found filter dirty and in upside down, recommend replacing more frequently. Client changed return grill, and wants to put filter there and remove filter inside blower compartment. Blower capacitor out of range still low. firstname.lastname@example.org. Blower dirty, see pictures. Evap coil doesnâ€™t have a secondary drain line just overflows onto unit. Condenser dirty coils on back side of unit especially bad. Washed unit. Top of unit still cracked. Compressor start capacitor email@example.com low. System appears to be low on r22 refrigerant see pressures, just below the freezing point. But with everything else going on wonâ€™t know for sure until all recommended repairs competed. With age of system and shape of system, recommend repair vs replace options. Went through entire ac system, cleaned and checked all parts.
Added new 16â€ return to living room wall. Increased the hard pipe return in garage from 16â€ to 18â€. Installed adjustable 18â€ 90 through ceiling in garage and 18x16x16 wye in attic to attach the new and old returns. Installed high flow return grille at new return location. Found 4â€ supply at bathroom disconnected and reconnected it. System is now running with much better airflow and is no longer restricted.
Add 2nd return to system to improve airflow to system and to extend life of unit. Current return undersized for unit and home. Would need to enlarge 16â€ duct to an 18â€ duct. And adding an 18â€ adjustable 90, as well as a 18-16-16 wye. Then connect the old 16â€ duct and a new 16â€ duct as well as 14-30 return filter grill and can. 650 original bid 572 Total 1222$ Emailed new estiment to client
Homeowner getting other estimates
Roseville California AC heating service AC heating maintenance AC heating diagnostic furnace not coming on not producing heat. found problem to be a plugged pressure switch port. cleaned pressure switch port and inducer assembly to help prevent pressure switch port from getting plugged by debris
Antelope California AC heating service AC heating maintenance AC heating diagnostic performed recommended repairs found during heating maintenance Replace blower motor capacitor. Tested system operation after replacement system operating with no failures
Antelope California heating AC service AC maintenance AC diagnostic AC not working no cool air AC diagnostic findings system trying to run / cool not working house is 87Â° inspection at outdoor unit found compressor overheated Open winding terminals. outdoor fan running has very bad vibration. causing top panel to start cracking will continue to damage top that is holding fan motor in place due to vibration. capacitors found bad compressor capacitor likely cause of compressor overheating do to system trying to run and not working possible damage to compressor has occurred. Repairs needed compressor called off to try and see if windings will open if windings do not open compressor will need to be replaced if windings open next step would be to replace capacitor. Replacement of capacitor needed to be able to test system operation. Cooled compressor down replaced capacitor turned on system checked operation blower capacitor still weak could go out at anytime and keep the blowe
Antelope California heating ac service AC maintenance Lennox package unit Electrical connections all tight no broken, burnt or overheating terminals. Electrical wire for condenser fan becoming brittle starting to crack capacitors compressor 35 reads 34.3 , outdoor fan 7.5 reads 7.5 , blower 7 reads 7.3 (good) Amp draw compressor 18.2 actual 14.28 , outdoor fan 2.8 actual 1.13 , blower 2.3 actual 2.14 (good) Refrigerant pressure is good Performed simple water wash on condenser coil as part of AC maintenance flushed drain line of sediment build up Blower
Installed 50 g ultra low nox antelope
Sacramento broken sewer main