Not only did I save money, but I received fast service from knowledgeable people. I called another company that I had used before and they made me wait 2 hours before telling me they couldn't help me. So when I called Crystal Blue and spoke to someone right away I was impressed. I will use them for everything in the future.
I have had 3 technician's out to my home thus far and each one was courteous, efficient and so friendly. It's been a long time since I have received service on this level.
Our AC unit went out when it was 104 degrees. Jordan was out the next day hours early and had us up and running in 10 minutes!
Michael, provided OUTSTANDING service, his customer rapport is truly professional. He responded in a timely manner with consideration to our time and was extremely courteous. A customer oriented technician of the highest caliber. mm
Great communication great customer service and fast install
friendly and good service
- Disconnect drain lines under sink for modifications of new sink dimensions - Install new under sink drain line and connect to sink - Provide sink and faucet for installation - Install new garbage disposal to replace corroded and worn garbage disposal - Garbage disposal comes with two year worry free guarantee - Cut water supply to building and remove existing emergency shut off valves - Provide and install two new â€œEZ Closeâ€ angle shut off valves - Water pressure tested and found to be high ( approximately 75 psi - Ideal water pressure 50-60 psi) - New water shut off valves tested for operation and for leaks using building pressure - Test unit by operating - Start up sequence and fine-tuning include
Performed A.C maintenance in Antelope. Unit is a Payne outdoor condenser on backside of house. Condensing coils are clean and free of debris. Checked all electrical connections and are okay no damaged or burnt wires. Checked refrigerant levels and are showing 118psi LowSide and 335psi Highside (Ambient outdoor temp 86*). Refrigerant levels are okay. Checked contactor and is in working order with no issues. Checked capacitor and is in range on compressor side showing 44.38uf which is okay. Fan side of capacitor should be 5uf +-6% and is showing 3.1 which is over the 15% mark and should be replaced. I recommend doing this repair to lengthen the lifespan of your unit. The capacitor is what delivers correct power and amperage to motors and compressor. If it fails there is a potential to damage more equipment than the capacitor. Repair Notes: Replace out of range capacitor with a new one of same style fit for the unit. The fan side of the capacitor is out of range by over 15%. This cou
Technician Taylor arrived on scene to investigate reports of problems with water heater. Technician discovered water heater to be 40 gallon natural gas Kenmore water heater from 2004. Technician found the water heater to be leaking from the top and recommends immediate replacement. Technician will supply proposals. Technician presented both proposals for client where she inquired about financing. Technician inform them of the financing a process and approval and they wanted to move forward. Technician attempted to apply for financing. Service Finance rejected application. Client stated they wanted to wait and look at other options because they could not afford it.
HVAC diagnostic - information provided to me from property management suspect a bad compressor. started diagnostic with testing and inspecting compressor. windings tested good, no direct shorts, ohmed windings good within specifications of manufacture, checked for any open circuits none. compressor should operate. Inspected all electrical wires good, tested dual run capacitor found capacitor is oversize for unit should be a 30 MFD has installed a 35 mfd. overtime will cause compressor to go bad. turned system on compressor started with no problems. checked refrigerant pressure found system low on refrigerant R22 causes a leak in the system undetermined where no big visible signs. inspected evap coil / air handler. Tenants complaining of low airflow upstairs found that to be caused by low airflow on return side no easy way for unit to cycle return air as well as blower motor and wheels are plugged / dirty restricting the air movement. Options to provide cooling back into property. R
Performed annual ac tune up 2008 Trane split upflow garage backyard. Tested system. Gave system bath. All parts in range dual capacitor 55-5 ok, contactor has been changed. Blower clean. Blower capacitor ok for now. Checked refrigerant, hold pressure for now. System running well at this time changed filters 2x 14-30-1.
Technician arrived on site to investigate reports of washing machine hose bibs leaking. Technician met with client and inspected problem. Technician found sheetrock to be opened up to expose entire washing machine box including hot and cold supply lines and 2 in ABS drain line. Technician supplied options for doing as little as just replacing a single hose bib up to replacing the entire washing machine box. Client's husband is currently at work. Technician will wait for response before moving forward. Tech will rebuild laundry box including 2 1/4 turn angle stop and drain adjustment Technician Taylor performed install per proposal and installed new washer box. technician cleaned work area of all trash and debris and tested to ensure no leaking. Technician collected signatures and payment
- Shut water off to existing faucet - Disconnect existing water supply for removal - Disposal of existing faucet included - Customer supplied new Standard kitchen faucet for installation - New faucet connections tested with building pressure - Test faucet by operating repeatedly NOTE - Minor rust and corrosion found on sink NO WARRANTY
- Shut water off to existing kitchen faucet - Remove existing kitchen faucet by disconnecting water supply - Disposal of existing kitchen faucet included - Customer supplied new Standard kitchen faucet for installation - New faucet connections tested with building pressure - Test faucet by operating repeatedly NO WARRANTY
Performed annual heating maintenance, 12 yr split upflow system garage. Tested system, working well at this time. Cleaned out blower compartment. Checked blower capacitor, 10@10 ok. Checked electrical connections all electrical wiring tight and ok at this time. Hot surface ignitor ok. Cleaned flame sensor and burners. Put everything back together tested system safety features. All working at this time. Resigning for another year
Customer has removed the old tub and walls in the hall bathroom and they want there new tub installed. No sheetrock repairs, level the tub off with grout underneath the tub. Waste line connections to be installed new and connected. When the tub is finished filled to the top and drained to make sure there are no issues or leaks.
Called customer and they cancelled.
Performed ac maintenance on electric roof top package unit. Went thru system first for heater to warm up house, cooler morning... then tested ac. System is from 1977. It is working for now just not running as good or efficient as it could be. Blower has a slight wiggle and vibration. All parts are working for now. Due to age of system want to watch how much money you put into system for return on investment. Change filter more often. Electrical connections ok at this time. Refrigerant ok at this time.
Performed annual heat maintenance on Lennox electric package unit roof. Unit is original from 1977. 42 yrs old. Went thru and unit is showing its age, blower is dirty, blower is also vibrating. Changed filter, in pretty roof shape recommend replacing filter more often. System running, just not as effiecntly as.
Provided plumbing maintenance water heater is from 1999 flushed water heater and inspected all plumbing fixtures throughout the house. Going to provide a estimate for water heater replacement.
Left estimate to install a puronic whole house water conditioning system, this unit will remove all the calcium and magnesium from the water with very minimal sodium use it also removes the chlorine from the water and the sand sediment dirt and debris has a limited lifetime warranty through the manufacture.