Michael did a great job, was very courteous, friendly, and thorough in checking out our AC system. The only reason I gave them 4 stars vs 5 was because we waited the estimated time for his arrival and he did not come. He had called earlier and told us he would be here at the latter end of the time frame but he ended up being unable to make it do to another job. We remade the appointment for the following Monday from 8-10. They called and said it would closer to 10 as he was waiting for a delivery. Unfortunately, it ended up being closer to 10:30, which would not have bothered me if it had been the first appointment. Either one alone would not have been a problem but since there was a seeming lack of respect for OUR time two times, I wondered if it was indicative of the attitude of the company as a whole, although he did mention that someone had recently quit which could definitely have caused the delays.
Tom was on time, informative, thorough and non-judgmental of why we needed a plumber. If we ever need your services again, we are calling you...definitely recommend you guys!
Sean came out and did some toilet rebuilds for our home and everything went perfectly ! He was very thorough and rechecked his work to ensure all was in perfect working order and kept the work areas picked up and clean. Thanks CBP for a Great Job ! -Kevin
Upon arrival found toilet to be constantly running. This estimate is to replace fill valve and flapper. We will drain toilet tank and remove fill valve and replace with new fill valve. The angle stop and supply is a one piece pull, push style angle stop we will re connect to new fill valve.if still in good condition After completing toilet rebuild attached to existing angle stop one piece supply and the angle stop connection to the supply was leaking we were placed with push to connect angle stop thereâ€™s pex coming out of the wall and install new supply line.
Customer has a 40 gallon propane water heater that is fluctuating itâ€™s hot temperatures. Which is a very symptomatic problem for a water heater in which is going bad. After going over many options with the customer They have decided to stick with a 40 gallon Bradford white tank heater and also have extreme interest in a full house filtration system. Halo five. Customer seemed very happy and satisfied with the information I gave her. So we will be sending an estimate today and looking forward to hearing back from our customer.
Out for estimate for adding mini splits 4 zones, 2 ducted and 2 ductless. 24, 12, 7, 7
Replace indoor evap coil. Take apart unit, remove side panels and top. Dissconnected fan. Reclaim refrigerant. Remove indoor evap coil, re nitro braze in new evap coil, pressure test with nitrogen, then vacuum system to below 500 microns. Then Factory weigh in refrigerant charge of 92.8oz of r410a, then reworked everything back up. During install found that system has both a txv, and a fixed orfice metering device. Not normal, but system is working for now. Tested system pressures ok at this time. House cooling. Gave unit a good water bath.
Performed ac diagnostic found system low on refrigerant, looks to be indoor evaporator coil, quoted repair options client want to think about it. Performed ac diagnostic
- Remove plants and shrubbery - Remove landscaping rocks and railroad timbers - Clear out chrushed gravel and stone - Excavate main sewer for replacment - Install up to 20 ft (linear ft) of heavy duty sewer piping - Replacemnt includeds new more accessible cleanout - Back fill piping and hand rack area - Replant previously removed plant life and vegetation - provide landscaping rock as decorative feel to walkway area - Provide Approx. 250 lbs. of concrete as added reinforcement at septic tank connection - Replace Previously removed landscaping stones and timbers
Except the down payment for work to be done on Thursday and Friday of this week left clean out open to relieve pressure and drainage for the next two days until we can arrive on Thursday to make necessary
To add ac to house would need, 20 feet high voltage wire, new breakers, disconnect and whip with fuses. Ac condenser and coil with 10-12 feet of lineset. Also need to rerun the drain line out from under house. Would also need to run new thermostat, new thermostat. Permits and title 24 testing
Performed furnace diagnostic 2003 Trane split system outside closet. Found gas valve not opening, checked for power at gas valve getting signal. Check control board, everything looks ok took picture. Tested gas valve needs to be replaced. Replaced Gas valve, switched lp kit. Tested system system fired right up. Due to age of equipment want to watch how much money we are putting into it, also keep an eye on the rust and water marks on platform unit has or is leaking water. Equipment operational at this time.
Clients have 2 split system westing house, one in the attic for upstairs. One in the basement for down stairs. Plus 2 tankless water heaters in basement. Downstairs furnace tested unit, unit cycled on, ran system tested system safety features. Cleaned burners and flame sensor. Tested blower capacitor email@example.com unit has had a control board replaced. Hot surface ignitor has been replaced. Upstairs furnace tested unit, unit cycled on. Found burner compartment door not attached. Cleaned burners and flame sensor. Tested blower capacitor firstname.lastname@example.org. Drain pan has rust in. Furnace drain lines ok keep eye on slope. Resigning up for the same plan they had before.
Run snake through outside cleanout to clear drain going to septic tank. Ran snake through clean out between septic tank and clean-out. Cleared blockage. Ran water and flushed toilets several times to assure blockage was clear. Uploaded pictures.
Performed annual heating maintenance on a 15 yr carrier heat pump package unit on the roof. Found unit still doesnâ€™t have a service disconnect. Have to turn unit on and off and main breaker box, not to code. Also the drain line has separated on the roof. See pictures. Re attached drain line, just pushed them together. Wonâ€™t last. Fix would be to remove and repair/ replace to make it go all the way to the gutter. Cleaned off leafs from behind unit. Checked parts ok for now. Capacitor bad email@example.com, dropped since last time. Control board ok.
Out to quote standby generators. Emailed quotes to client. Performed load calculation to see how big a generator they would need. And with room to expand recommend the 20kw
Cannot add ducts to needed rooms due to no access to the rooms location. Furnace showing signs of failure with rust building up in heat exchanger. Potentially a hazard if heat exchanger breaches.
Removed the wall heater and pulled the vent out of the wall, closed both sides with plywood. Ran a loop system after the well tank and attached to the softener, filled the brine tank with 5 bags of salt. Turned the water on with no leaks, flushed the system for 25 minutes and 30 minutes of regen. Set the hardiness to 17, let the water run and tested at the bathroom sink which showed no hardness. Customer is provided a one year parts and labor warranty.