Technician came out quickly but I never received a promised quote for an HVAV or a split system. He made another appointment but then never showed up. Very disappointed. Bad service.
Very professional development
#no. Set for Monday between 9-10 for myself and Mike to go out
Changing swamp cooler belt, installing new customer supplied pads, installing a new water float. And draining and cleaning the swamp cooler pan.
Called client to go over new price with me installing there supplied pads. No answer, mailbox full. New quote has New belt, and new float. And installing there pads x3.
Performed swamp cooler inspection. Found what appears to be original swamp cooler showing age. Water pads donâ€™t fully cover the doors. Some air gaps. Found unit leaking water thru float constantly. When float seals it sprays out of nut connection from water line. tightened connector water leak stopped Motor looks ok. Belt and pulley a little loose. Belt is starting to crack, But holding. And pulley appears to missing proper set screw. System is working just showing age. Went thru swamp cooler to find any and all issues that might come up.
Completed plumbing maintenance and found no leaks in the water system, water pressure is 50 psi, lavatory faucetâ€˜s have sediment inside the air Raiders the toilet fill valve is a little slow also do the sediment and the hall bath shower cartridge also seems to be slow. Signed homeowners Up on The membership which includes plumbing inspection, heating and air-inspection and maintenance
Will pull toilet for access and run 300 machine up to 1hr service includes camera survey as well there is a crack in tank upon arrival itâ€™s not leaking ran line several times before it drained out was able to camera and locate problem spot broken pipe catching toilet paper depth 3to 4feet on back side of building near water main at corner do not use paper until this is fixed we will provide estimate for repair additional work may be requierd to resolve issues long term
Technician will perform exploratory to locate water leak and assess for repair. Technician found existing inch and a quarter water supply line to house failed repair coupling. Technician will install Union with proper fittings and complete with pressure test. Repair okay had customer inspect technician will backfill and compact. Price includes Parts labor in one year warranty leaks labor.
Swimming pool troubleshoot existing tankless water heater
40 gallon gas water heater install
Sewer backed up. Cool plumbing. Cool
Tankless water heaters. Pilot hill plumbing. Pilot hill
Water heater replacement. Cool plumbing. Cool
Water heater replacement. Cool plumbers. Cool
Auburn storm drain repair