Client stated condenser will run for 5 minutes then stop. Checked charge and it was correct. Tested amp draw of a total of 19 amps out of 50 on the breakers. The breakers where getting vary hot. Breaker would trip after 5 minutes. Would like to replace breakers. Customer approved replacement of double 50 GE breaker. Replaced breaker. System stayed running and breakers did not get hot. System is operating at this time.