Good experience, I recommend them
Scott was so awesome! Knowledgeable and very thorough. He explained everything to me in detail and also covered the importance of having our heat and air unit serviced twice a year to keep in in top working condition. He had the correct part in his van and it did not take long to fix it and have the air conditioning back and running. Thank you Scott! We also love the texts Crystal Blue sends letting us know who is coming, what they look like and what time. They also provide a view of where the driver is on a map and when he will be arriving to the house. Thank you Crystal Blue! We will definitely recommend you to all our friends and family.
Brad and Tika were very personable & professional.
Grayson was knowledgeable, thorough, kind and willing to work with us.
Crystal Blue Plumbing was professional and very thorough throughout the start of our situation. Grayson was knowledgeable and took his time in assessing our issues.
We were very satisfied with our routine maintenance today..he was professional and courteous. ..thank you for being great company.
Second time dealing with keiton & always polite & professional.
The two young men who serviced our air conditioning system was very polite & professional.
Found bad low-voltage wiring at outdoor unit not turning condenser on Repair electrical for outdoor condenser replace electrical wiring from wall to condenser.
replace 1.5 Ton Evaporator Coil and Condenser. Scope of work to include: Removal and disposal of old equipment per epa. Installation of new evaporator coil. Set and fasten condenser in place. Brazing connections. Will tarp and cover floors, clothing, anything of customers necessary to protect from dust / damages.
On arrival customer would like estimate for customer supplied parts all estimates are included in the email
Annual plumbing inspection found. Water heater code issues, missing expansion tank, drip leg, strap. Hall bathroom sink has plastic supply lines. Put stickers on garbage disposal and water heater. Water heater looks good 2013 model
Breakers where not labeled properly at panel so the power we thought was a outlet was a lightly circuit. Moved and took power from the outlet. Tested all lights and out letâ€™s and fan kept going.
Installation of Whole House Fan Cleaned up all debris. Tested fan in all modes, Went over operation with customer. Fan is operating at this time.
Replacement of electric split system. Upflow furnace in closet. Recommend: 2 Ton Trane 14 SEER XR14 and matching furnace TEM4 (80%). Scope of work to include: Pull permit. Removal and disposal of old equipment per epa. Installation of new furnace in closet. Set and fasten condenser in place. Brazing connections. New pad, new whip, new disconnect. New thermostat. Tape and seal register boots. Duct testing per title 24. Technicians will wear masks, gloves and other necessary personal protective equipment. Will tarp and cover floors, clothing, anything of customers necessary to protect from dust / damages. Work will take 1 day to complete.
Took 180 deposit for hole house fan, Installed condenser fan motor. Will return next Thursday morning to install hole house fan
WO# 144510131. This estimate is to replace toilet flange in the first stall of the womenâ€™s restroom after attempting to do a pull reset found that the flange was deteriorating and had broken chips off of the flange We will jackhammer around flange to remove flange jackhammer about a foot deep to attach to pipe we were pour back Concrete around on flange and do a rough concrete patchThis estimate does not include any tile work that may need to be done a couple tiles may need to be removed in order to replace flange. We will remove the tiles if necessary And go back with a rough patch of concrete.
Client stated unit was humming out side but not coming on. Verified customers concerns. Found capacitor to be internally shorted and the contactor to be severely burnt. Client approved replacement of both parts. Client also went with club membership. System is operating at this time. Changed filter with client supplied one
Opened ticket to view photos to order equipment. Added POâ€™s, sorry Glenna probably didnâ€™t do it right - Brad
Client stated unit was not cooling and out door fan was not coming on. Verified customers concerns. Inspected capacitor and it was out of spec. Replaced and condenser fan kicked right on. System is cooling at this time. Client went with club membership
Customer stated out door unit sounded like it wanted to turn on. Verified customers concerns. Inspected out door unit. Found that the capacitor was mushroomed out and out of operation. Contactor was black and sparking, Condenser coil was vary dirty. Replaced parts and cleaned coil. Customer went with club membership
Out to estimate replacement of electric split system. Upflow furnace in hall closet, condenser in backyard. Gave client single stage and two stage options for replacement. Client wants to move forward with single stage estimate. Work will be performed on Thursday, August 20th. Client did not wish to leave down payment at this time.
Copper line in garage is leaking will have to have plumber come out later this afternoon.