Very professional, and communicates well. Very detailed inspection.
Crystal blue and Michael and Angie did great job of correcting a mess caused by another contractor. They advocate for use and performed as promised. These people and this company is great. They are our HVAC contractor in the future.
Very professional & knowledgeable courteous and helpful
Customer stated hole house fan will not come on. Found motor to be thermaly overloaded. Motor would have to be replaced. Customer would like to go with quite cool hole house fan replacement. Took 100 deposit and 49 for diag .
Client stated unit was blowing warm air. Found unit low on r22 added dye and charge. Next Thursday at 9:30 am. Come back to check for leaks
After doing the plumbing inspection everything in the home seems to work properly. My only concern is that they have a very high water pressure fluctuating between 78 and 81 psi. Also the home has a gate valve for the emergency whole house shut off I recommend getting a ball valve which are much more likely to last longer and not fail. I left estimates for the PRV and PRV with ball valve. Customer seem to be happy and satisfied with the job performed.
Recovered old refrigerant. Sweat off old compressor. Brazed on new compressor. Pressurized system to 350 psi for 1 hr with no drop in Pressure. Leak checked all connections. Pumped down to 375 microns. Filled with 7.1 lbs of 410A System started right up. Has a 20 degree temperature split. System is operating at this point.
Customer stated unit was blowing warm air. But is was running, verified customer concerns. Inspected furnace found no fault codes and system was operating as it should. Had. Zero temperature split. Should see any where from 15 to 20. Inspected out door unit, found that after checking charge that the compressor was not running. Attempted to cool the compressor down with water. Then attempted to jump start it with a hard starter kit. Compressor is pulling over 200 amps when attempting to start, compressor is seized. Compressor is still under warranty, Will be installing compressor Wednesday. Total to be collected $1,750 Took 10% down today of $175
Performed a.c maintenance in Foresthill. Unit is a Trane xl14 package unit on side of house. Is about 5 years old. Checked all electrical and is okay. Checked contactor and is okay. Checked capacitor for blower motor and is okay 7.5uf and showing 7.39uf. Checked capacitor for compressor and is okay 70uf and showing 69.7uf. Blower motor and wheel are clean and free of dust. Compressor compartment has some dirt and will remove. Tested refrigerant pressures and are showing 110psi LS and 224psi HS.
Technician Taylor arrived to investigate reports of a water heater issue. When technician arrived he discovered that problem actually was with a heat pump that we installed. Client stated that once you spoke with the call center we stated we had no record of the install. Client presented two original crystal blue invoice papers for a new HVAC system and water heater. Technician contact dispatch to send out HVAC technician to aid client.
Re signed up on another year of membership Membership Re designed partial duct replacement, connecting to plenum directly. This would be running a duct from the plenum to the new silver ducts and reconnecting it all. 8â€ from plenum, new 8â€ start collar, and 8-6-6;wye, 1 8â€duct. And added register in bathroom so cat doesnâ€™t fall into duct again. Tested system much better airflow. Clients happy with airflow
Performed annual heating maintenance, 5 yr gas package unit side of house. LP. Ducts under house are mix of silver and grey alumiflex, not in great shape, and donâ€™t get even air flow. To fix that we would have to redesign the duct system. But we can always just re attach the fallen duct. Changed filter. Tested system safety features ok. 12-4 toe kick
Install mobile home Coleman down flow furnace 3 Ton unit p, new roof jack, flue pipe, pigtail gas flex. Add A/C, add Refrigerant line 3/4â€ run electrical, install electrical disconnect and whip. Install all new ductwork with new cans and connections, seal ductwork.
Performed furnace diagnostic 14 yr mobile home unit. Furnace has been moved and then someone covered the return air vent. Into the walk in closet. Most of the floor registers are missing in the home. Which is effecting air flow. Main supply duct to side of house in bad shape, sitting on the ground. Furnace appears to have been moved at some point. Itâ€™s now in a closet behind the house. Water heater doesnâ€™t have a flue pipe attached, itâ€™s off to the side. Floor under swamp cooler falling apart. See pictures and ceiling in middle of home appears to be leaking. System does work for now, tested and cycled system multiple times ok. But due to age shape and neglect. Might want to replace system. Found unit 29 in bad shape, unit works needs big maintenance. Floor falling apart under swamp cooler.
Arrived at job. Turned system on, put gauges on system. Found system low pressures. 4 ton 12yr old gas split
Install navien 240a under house exhaust through existing forced air pipe there's power near by will need a outlet installed Mike is coming to service HVAC he could do outlet for me will run 3\4 feed for recirc at kitchen and master bath
Flush unit after regulator is fixed re check system replaced flow sensor cleaned filters operations normal
Older unit in basement or mud room called in to Navien and turned on recirc pump on bank of 8 5 in the on position purged circ line tested gas pressure on incoming found low pressure unit is starving for gas customer is going to call propane company to connect regulator