Very professional, and communicates well. Very detailed inspection.
Crystal blue and Michael and Angie did great job of correcting a mess caused by another contractor. They advocate for use and performed as promised. These people and this company is great. They are our HVAC contractor in the future.
Very professional & knowledgeable courteous and helpful
Performed a.c maintenance in Foresthill. Unit is a Trane xl14 package unit on side of house. Is about 5 years old. Checked all electrical and is okay. Checked contactor and is okay. Checked capacitor for blower motor and is okay 7.5uf and showing 7.39uf. Checked capacitor for compressor and is okay 70uf and showing 69.7uf. Blower motor and wheel are clean and free of dust. Compressor compartment has some dirt and will remove. Tested refrigerant pressures and are showing 110psi LS and 224psi HS.
Technician Taylor arrived to investigate reports of a water heater issue. When technician arrived he discovered that problem actually was with a heat pump that we installed. Client stated that once you spoke with the call center we stated we had no record of the install. Client presented two original crystal blue invoice papers for a new HVAC system and water heater. Technician contact dispatch to send out HVAC technician to aid client.
Re signed up on another year of membership Membership Re designed partial duct replacement, connecting to plenum directly. This would be running a duct from the plenum to the new silver ducts and reconnecting it all. 8â€ from plenum, new 8â€ start collar, and 8-6-6;wye, 1 8â€duct. And added register in bathroom so cat doesnâ€™t fall into duct again. Tested system much better airflow. Clients happy with airflow
Performed annual heating maintenance, 5 yr gas package unit side of house. LP. Ducts under house are mix of silver and grey alumiflex, not in great shape, and donâ€™t get even air flow. To fix that we would have to redesign the duct system. But we can always just re attach the fallen duct. Changed filter. Tested system safety features ok. 12-4 toe kick
Install mobile home Coleman down flow furnace 3 Ton unit p, new roof jack, flue pipe, pigtail gas flex. Add A/C, add Refrigerant line 3/4â€ run electrical, install electrical disconnect and whip. Install all new ductwork with new cans and connections, seal ductwork.
Performed furnace diagnostic 14 yr mobile home unit. Furnace has been moved and then someone covered the return air vent. Into the walk in closet. Most of the floor registers are missing in the home. Which is effecting air flow. Main supply duct to side of house in bad shape, sitting on the ground. Furnace appears to have been moved at some point. Itâ€™s now in a closet behind the house. Water heater doesnâ€™t have a flue pipe attached, itâ€™s off to the side. Floor under swamp cooler falling apart. See pictures and ceiling in middle of home appears to be leaking. System does work for now, tested and cycled system multiple times ok. But due to age shape and neglect. Might want to replace system. Found unit 29 in bad shape, unit works needs big maintenance. Floor falling apart under swamp cooler.
Arrived at job. Turned system on, put gauges on system. Found system low pressures. 4 ton 12yr old gas split
Install navien 240a under house exhaust through existing forced air pipe there's power near by will need a outlet installed Mike is coming to service HVAC he could do outlet for me will run 3\4 feed for recirc at kitchen and master bath
Flush unit after regulator is fixed re check system replaced flow sensor cleaned filters operations normal
Older unit in basement or mud room called in to Navien and turned on recirc pump on bank of 8 5 in the on position purged circ line tested gas pressure on incoming found low pressure unit is starving for gas customer is going to call propane company to connect regulator
Foresthill California HVAC service AC heating maintenance AC heating diagnostic performed heating maintenance checked air filter, gas pressure, and operation of system. Cleaned burners, flame sensor and spark igniter. system operation normal at this time. found no problems or issues with system. no repairs needed at this time.
Foresthill California heating AC service AC maintenance ac diagnostic dryer vent repair ducting repair. Diagnostic findings dryer vent disconnected underneath house allowing dryer lint to build up creating fire hazard. cleaned lint build up from underneath house 1/2 - 1 inch thick on ground walls, floor joist and insulation. Cleaned 5 x 8 area top to bottom of fire hazard. repaired dryer vent duct secured and strapped to prevent this from happening again. Did a basic clean on dryer vent as a courtesy to customer while I had venting apart. Work on dryer vent has 1 year parts and labor as long as it's not caused by physical damage.
Technician performed full inspection on shower valve install looked at Finish trim. Notify customer was assembled incorrectly technician reassembled works great
Foresthill California heating ac service AC maintenance Trane gas package unit propane visual inspection no burnt or overheated wire connections. contactor contact points good no pitting or burning. wire connections tight in disconnected and on contactor control board connections look good. Capacitors compressor 70 reads 69.2 outdoor fan 7.5 reads 7.5 capacitors good Amp draws good Water washed condenser coil cleaned inside of unit out Found water in drain pan caused by drain line sloping wrong way debris cleaned out from underneath and bumped up words. made customer aware when cleaning around unit to make sure drain line is pushed down Found no problems with unit at this time no recommended repairs
Plumbing Forest Hill leak detection Atwater supply estimate for new line install