Recovered old refrigerant. Sweat off old compressor. Brazed on new compressor. Pressurized system to 350 psi for 1 hr with no drop in Pressure. Leak checked all connections. Pumped down to 375 microns. Filled with 7.1 lbs of 410A System started right up. Has a 20 degree temperature split. System is operating at this point.