I was really amazed at the pictures of our equipment up in the attic - I’m not crawling up there but it was great to see what was working and what minor work needed to be done. The pictures of the system were really great!
I have been using Crystal Blue PHA for about four years now and have only had a single experience which was ‘less-than-desirable’; always incredible service and the technicians are knowledgeable, helpful, friendly, and go above and beyond. Top Marks!! Today’s experience with Sam Torres was no different! First rate!! Thanks Sam! Hope to see you again!
Excellent, thank you
He goes the extra mile!!!
Everything was perfect.
Service and repair value at my mother's ranch after multiple jobs has been consistently excellent. On time, competitively priced, and repairs executed in a timely manner. Popeye is a very pleasant professional to have on the job.
Chrystal Blue Came to my rescue on the Wednesday before Thanksgiving. Did a temporary fix which worked great. Came out a week later and completed the work. Sam was great. He explained thoroughly what was to be done. Was efficient, respectful, courteous and did a great job. I highly recommend this company.
Very Satisfied, job well done. Thank you, Brandon. I have cold and hot water back in my home, pressure good. Looking forward to schedule an appointment to have my home inspected. Ince again, I thanking Brandon and you for you professional service
Arrived on time. Completed on time. Perfect Job Replacing Water Heater.
We discussed possible repair or replacement solutions for water heater water heater 7 1/2 years old will need to be serviced at some point to operate correctly review possible replacement repair options and possible financing additionally discussed the benefits of the club membership program
Customer has a shower valve that spins and is hard to get hot, turned the water off and removed the old cartridge. Installed a new delta cartridge and installed the shower trim, turned the water on with no leaks and hot is on the left.
Technician Taylor arrived on scene to investigate reports of water heater leaking. Technician found client to have two tankless Noritz units mounted in the garage. Technician found the hot supply from the one mounted on the right had type m copper running to the wall that was badly corroded. Technician recommended replacement of that section client agreed. Technician acquired parts and performed install. Client also mentioned that her recirculation pump had burned up. Technician confirmed and recommended replacement. Client accepted. Technician will acquire parts and return. This proposals for the installation of a handheld shower and clients guest house. crystal blue plumbing heating and air will furnish and install all labor and materials necessary to complete the following scope of work - protect clients belongings - shut off water to work area - disconnect existing shower head and disposal properly - install new high quality dark finish handheld shower head - test to ensure proper
Technician Taylor arrived on scene to provide proposal for the installation of a dedicated gas line from gas meter to laundry room. Client is the tenant and intended on paying. Client moved in on Monday and realized that there was no gas line to hook up his dryer to. Flight was interested in a proposal to install a gas line to the laundry room. When technician gave an idea of the ballpark numbers client immediately changed mind. Client expected less than a grand. Stated they would rather just purchase an electric dryer.
Performed system maintenance Lincoln. Some one added a filtered fresh air vent into the return plenum. Filter is very very dirty. System hasnâ€™t been serviced in awhile. Furnace carrier 16 yrs old. Blower capacitor firstname.lastname@example.org, low well below manufactures recommend specs. Recommend replace. Duct work silver flex sealed with mixing boxes, found one mixing box on platform has hole in it big enough to put a finger in. Hot surface ignitor ok 60 ohms. Cycled heating system with nest thermostat, then switched to ac. Dual capacitor ok 55-5, contactor has been replaced. And system has hard start kit. Data plate for ac has worn off. Ac refrigerant pressures slightly low, but normal for it only being 50 outside. Signed up on membership, installed new 10 mfdblower capacitor. And sealed hole in mixing box at no charge for signing up today.
Performed wall furnace diagnostic, 20+ yrs old Williams doubled sided wall furnace. Not heating, found the gas pilot not on, tried lighting wonâ€™t stay on. Took out the thermalpile and cleaned it. Then or it to stay on, didnâ€™t come on right away. With thermostat on unit should have fired right away had to jumper it at gas valve to get unit to lite. House was cold so let system run for 30 mins before adjusting thermostat to see if it working correctly. Found one of the screws that holds the burner in place loose. Found safety switch has metal connections not covered. Covered them but as the line moves the unit turns off loosing the pilot. Recommend due to age replacing unit vs repairing. Going with the repairs today, trying to get it to last thru the end of this yr.
Upstairs unit gas valve not working, tested gas valve board sending signal 24v just not opening. Also inspected board, board looks ok. Removed old gas valve and replaced gas valve with oem gas valve. and tested system operational at this time. Cycled system on and off to verify working at this time.
Remove old unit and install new double sided gas wall furnace. Connect gas valve and install new thermostat. Includes framing of new unit if needed. Price only good for 7 days from this estimate. Normally $2350.00. 50k BTU Installed new double sided wall furnace tested heating customer happy with the installer left
Upon arrival customer would like an estimate to run a new cold water line and install a pot filler for stove. Went over the estimate with the customer. Customer is remodeling and will call is when the granite backsplash is removed.
Performed diagnostic on upstairs heater, found that unit is not turning on the gas valve. The gas valve is getting 24v power it is just not turning on. Need to replace gas valve and test system. Blower working ok at this time. Scheduled replacement next Friday 8-10 prefers closer to 10. Part is on will call at us air.
Install 50k double side wall furnace with thermostat and gas valve. Framing included if needed
Discussed various options for toilet installation and explained a toilet operation our waterways gravity feed so forth I looked at washing machine and hoses are rubber hose is a potential for a replacement there to avoid any possible issues in the
Remove and dispose of old double sided wall furnace, install new unit, connect gas valve and new thermostat. Framing included if needed
-Install a 4 piece shower kit. -will have to cut out existing unit and dispose of it will also replace shower valve single handle. -Make repairs to leaking drain pipe if any found. -For the shower tub we need to open up wall and replace old mixing valve with new valve and new cartridge. -this requires us too shut water down and cut into lines near valves. -then we would drain lines completely and solder on new valve. -the new valve will have a nice beauty plate installed to cover. -This would include changing out tub diverter and Shower head -The sink will have to remove old sink from vanity and counter top. -after removing and disposing of old sink we will then properly install new sink. -In the downstairs bathroom we would be replacing the entire vanity and sink with new plumbing and supply lines replacing with new vanity and sink that we provide. -we will re dap the counter top and re dap areas of bathroom that could use improvements. -Also including whole house filtration sy
Will shut water down and drain down. Will cut and replace 3/4x3/4x1/2 fitting with new uponor parts. One year parts and labor. Will tighten hot side wide spread faucet in master bathroom. Returned to install new pex tee that was determined to be leaking, upon diagnosis i noticed the tee was covered in calcium build up but was not wet at all. The insulation above the fitting showed signs of water mark, above the tee is a tub waste and overflow. Checked the overflow and the gasket wasnâ€™t tight enough to create a strong seal, tightened the gasket down solving the leak. Tightened the two lavatory faucet handles straightening the handles as well, customer is extremely happy and satisfied with the work performed.