Brad was very professional and thorough in his estimate. He explained all charges clearly and gave me more information to read on the fans.
Scott and his partner were pleasant to work with, I’m very pleased with their service. As far as the iWave-r and MERV filter functionality, I’m still waiting for a great result. I still can’t live in my house because I still have allergic reactions whenever I enter my house. Spores are still lingering.
Excellent! Very happy
Did great. Very nice guy
We were very pleased with your staff worker Scott Petty. we will recommend your company to our friends
I was really amazed at the pictures of our equipment up in the attic - I’m not crawling up there but it was great to see what was working and what minor work needed to be done. The pictures of the system were really great!
Out to estimate replacement of gas/ electric split system. Replacement of gas/electric split system. Upflow furnace in garage. Scope of work to include: Removal of old equipment per epa. New pad, new whip, new disconnect, new thermostat. Duct testing per title 24. Work will take 1 day to complete. 1 week out for install at this time.
Call icemaker out to gain access to floor drain Cable snake floor drain to begin water flow process After establishing waterflow coordinate with staff and set up jetter equipment Open clean out outside to verify good water flow Begin drain maintenance program for management to carry out Start up sequence for drain lines and icemakers included
Performed ac diagnostic 25 yr old rooftop Trane package unit. Found unit running just very high refrigerant pressures. Ecobee thermostat operational. Started to clean condenser coils numbers went way down. 66/260 went to 60/190... water coming off coil brown to start. let system run to verify working and Inside house dropped 6 degrees. System working well at this time Signed up on annual maintenance plan, and performed the ac visit today to help lower the costs.
Performed ac diagnostic Lincoln. 15 yr old Split carrier system. Found trying to turn on, makes sound but doesnâ€™t run. Tested dual capacitor found bad. Changed dual capacitor to test system, system operational. Gave condenser coils a bath with water. Draining out primary at this time.n Signed up for 1 yr maintenance plan, with ac tune up, furnace tune up and plumbing inspection
After looking at the customers toilet I could find multiple problems customer had all the parts needed for toilet I explain to him what I would need to do in order to make the fix he was enthusiastic about the education I gave him but was not happy with our price wants to talk it over with his wife and may possibly do it himself. He also wanted to talk to his landlord to see if he could be reimbursed for fixing the toilet. I also went to test house water pressure while waiting for a callback from the landlord I found a broken air raider on hose bib and i told him the price and he said only if the landlord wants to reimburse him for the air raider.
Out for estimate to install no whole house fan. No existing fan. High voltage electrical existing in attic. Very well ventilated attic, access in master bedroom closet. Client reviewing other bids, best offer so far was for $1800.
Customer was looking to get an estimate on fixing his sewer mainline from the clean out in the side of the house to the city connection. I ran a camera for the customer and about 45 feet down the line there is blockage and build up. I could see a slight belly in the pipe but due to the water and blockage I could not see the pipe well enough to give a trenchless estimate. After going over this with the customer he has decided we can come back to hydro jet the line. Which will clear the pipeline and we then can run a video camera inspection to make a better educated decision on how to Repair the belly in the sewer line.
Reviewed various installation options along with different decorative aspects of kitchen sink and Fossett customer would like to confirm our ideas with a fellow family members and then decide on which design they like best
This estimate is for adjusting a PRV where I had to dig down fully expose PRV take a look at the pipes make sure everything was in good condition before working on PRV. The house water pressure was at 40 psi after doing the adjustment the house is now between 65 and 75 psi.
Talk to Steve about the options of fixing it we went with the adjustment today readjusting the pressure up to 60 PSI where the house should be the sprinkler system is now functioning properly which it wasnâ€™t before. This work is not warrantee or guaranteed it is just a diagnosis with a quick adjustment to PRV.
Find leak in system where refrigerant is escaping. This includes tear down of unit to access evaporator coil in attic. UV light to search for fluorescent dye in system to trace leak. And adding 1lb of refrigerant to keep system cooling properly. Added refrigerant to system until Sub Cooling levels are correct for unit and coil. Looked inside of coil in attic attached to furnace and did not find a leak and no fluorescent dye. Checked condenser coils and near compressor and found no leaks. Will need to return again when system loses refrigerant and try to find leak at later time. Customer will call if system is not cooling again.
Customer has a Kholer Numi toilet and the display screen has stopped working, upon diagnosis I noticed water coming out from under the toilet. Further diagnosis with Kohler tech support and installing the new screen we determined that the back panel power supply got wet and fried. Customer wants to just purchase a new toilet and will contact us to come out and install the new Kohler Numi toilet.
Performed diagnostic in Lincoln. Unit is a Goodman condenser on back side of house. Unit is running and operating. Checked refrigerant levels after last tech charged system. Refrigerant levels are fine showing 128psi Lowside and 325psi Highside. Went up to attic to look at evaporator coil in furnace and all looks okay. System has incorrect sub cooling and super heat levels. System is low on refrigerant and will need to come back out to do leak search. System is leaking more refrigerant than recommended levels of leakage.
Replaced filter cabinet, new 4â€ merv 11 filter. Will follow up in 1 week to see if conditions improve.
Got to unit running, making extra noise. Hooked up gauges system still holding refrigerant. Compressor looks to be weak. Found disconnect hot to touch, checked electrical all appears tight and ok at this time. Turned system off and cooled off unit with hose. Tried to run system again, system ran like normal for a few seconds then you can hear the bypass opening. Tried to pump down the system at 90 psi compressor bypass opens up, weak compressor. From here a compressor is 7-14 days from factory. Condenser and coil, openings next week.