I was referred to Crystal blue by my best friend and he was right. It was a pleasant experience. The tech was well trained and professional. He had it working in no time and the price was reasonable. I will recommend Crystal blue to all of my friends . Thank you very much.
Excellent service rep 😉
Ali Opeyany was polite, courteous, and very eager to answer any questions I had. Thanks for the great customer service and keeping my home systems up and running efficiently.
Great experience, very professional
Was booked and fit us in. Got heater working same day.
Fantastic service and staff!! Continue with the professional work and exemplary customer service. Thanks Michael!!
Performed platinum plumbing inspection of single family dwelling. Looked at all fixtures and drain lines. Everything is in fair condition for age of home. Found water pressure to be to high and gave customer quote to install pressure reducing valve. Also gave customer quote to install a new garbage disposal in kitchen sink. Drained water heater as part of maintenance requirements by manufacturer. Water heater is from 2007 and in good condition.
Performed annual ac maintenance on 16 yr gas package unit ground. Washed unit changed 14-25-1 filter. Checked refrigerant after unit stabilized. Found small dead frog behind circuit board. Removed. Board looks good no burn spots. Checked wiring all tight. Contactor a little worn, keep an eye on it. Fuses and disconnect ok. Blower motor a little dirty working at this time. Plenums for side shot to unit small, so recommend keeping filter clean so it doesnâ€™t restrict airflow. 18 degree temp split.
Performed system check up Lincoln. On a 16 yr split system side yard closet. Found system with broken disconnect, see picture. For code condenser doesnâ€™t need disconnect so close to breaker panel. Condenser Unit is too close to wall. Refrigerant pressure ok. Temp split 18-20... 80 degree air going in 60-62 degree air temp average. Register in master bedroom faces the wall not the bed, master bathroom has a floor register. Filter is in a stamp face grill not a return air filter grill. Blower is dirty blower capacitor ok. Filter use to be inside unit. Duct work to garage is uninsulated alumiflex with holes in it. Multiple holes, see pictures. Rest of ducts are hard pipe. Went thru system today to see how old system is and in what shape itâ€™s in.
Waste arm and trap are leaking upon arrival may need additional work to correct this issue .. price is for clearing the drain only.cleared line tested good no leaks
Performed ac diagnostic Lincoln. Found bad dual capacitor. Need to replace dual capacitor to get system to run, then need to look at start amps and running amps for fan motor and compressor. Might need refrigerant or even a hard start kit. Wont know until system is up and running if it needs anything elsE. Got system up and running tested refrigerant, numbers got better gaffer cleaned coil. Need to keep an eye on start amps for compressor. Might need a hard start kit eventually. Change filters more frequently. Signed up on the maintenance plan.
Need to get material cost
Run cable through clean out to unclog. Ran cable through 2 inch kitchen sink clean out to unclog line servicing kitchen sink, laundry and shower drain. Ran cable approximately 30 feet to blockage and 60 feet total. Had kitchen sink and shower faucet running cold water while cleaning line. Line is clear, unknown blockage. Did not pull any material back to indicate cause of blockage. Flat rate labor 6 month guarantee.
Left estimate to dig up a small section of dirt right around the water meter to gain access to the three-quarter PVC line, repair the broken piece of pipe using new coupling and a small section of PVC, test to make sure itâ€™s no additional leaks ( if additional leaks options for repair will be given) #no The homeowner was asleep due to working nights I spoke with your mother we are going to have to follow up with the homeowner tomorrow
Performed ac diagnostic 29 yr old Goodman system, working at this time. Turned on unit system fired right up. Checked refrigerant ok, checked filter, checked airflow. System cooling at this time. Could be the breaker as before. Checked disconnect, electrical ok Checked breaker bad, breaker burning and falling apart. Need a new quad breaker.
Customer stated that garbage disposal was jammed and not draining. Upon arrival customer stated that basin on garbage disposal side had drained but was still not working. Used garbage disposal Allen tool to unjam and checked reset. Garbage disposal is working fine, ran lots of water sink is not clogged. No charge to customer.
Lincoln California installation of swamp cooler. when unit was originally installed new unit had problems running due to electrical field interference of 54v through other side of electrical wiring when no wiring was hooked up this was not cut before new installation and caused original motor to burn electrical windings. installation technician run new wiring to the agreed amount of $450 still had problem had electrician come out and diagnose and try and fix problem still had problem. had lead service install technician came out. found problem determined it was caused by electrical field interference electrical power back feeding through insulated wiring inside of Romax line had to run independent electrical feed lines from switch to swap cooler to prevent electrical field interference. will not charge for the additional work just the original amount agreed upon at $450 no additional.
Water was shut off at stops on shower valve turned on tested good flow at fixture.#no Nc
Electrician to come and fix electrical issues. Need to collect for this invoice.
Diagnostic system needs servicing need to blow out primary drain line and sign back up on the maintenance plan. Blew out drain line lots of debris in line draining much better at this time. Every service need to verify draining correctly. System has lots of scaling from coil to keep an eye on.
#no called contractor to get info for btu of smoker and permits from city of Lincoln