Service and repair value at my mother's ranch after multiple jobs has been consistently excellent. On time, competitively priced, and repairs executed in a timely manner. Popeye is a very pleasant professional to have on the job.
Chrystal Blue Came to my rescue on the Wednesday before Thanksgiving. Did a temporary fix which worked great. Came out a week later and completed the work. Sam was great. He explained thoroughly what was to be done. Was efficient, respectful, courteous and did a great job. I highly recommend this company.
Very Satisfied, job well done. Thank you, Brandon. I have cold and hot water back in my home, pressure good. Looking forward to schedule an appointment to have my home inspected. Ince again, I thanking Brandon and you for you professional service
Arrived on time. Completed on time. Perfect Job Replacing Water Heater.
I would love nothing but to hire your plumbing company to do the work.... however, $1,800 to hook up a $600 vanity is too expensive! Especially because we need to sell the house, not live there.
Fantastic experience from beginning estimate to completion of repairs.
I was referred to Crystal blue by my best friend and he was right. It was a pleasant experience. The tech was well trained and professional. He had it working in no time and the price was reasonable. I will recommend Crystal blue to all of my friends . Thank you very much.
Excellent service rep 😉
â€” Drain Jetter Clog â€” - Open sewer line to gain access to kitchen sink line - Cable snake drain line to establish better flow - Use Jetter for â€œHydro-Scrubâ€ of sewer - Provide BioOne drain maintenance solution for customer to apply â€” High Pressure Solution â€” - Locate and shut down water to access malfunctioning valves - Cut open drywall to cut water distribution supply and modify - Remove existing shut off valves and replace with new â€œEZ Closeâ€ shut offs - Pressurize and and start up pressure fine tuning included - Insulate piping to help prevent freezing - Replace drywall and/or install access panel for future use
We will remove old equipment per EPA regulations and install a Trane Furnace XV80% Two Stage Heat with True Variable Speed Blower model number: TUD2C100B9V5VB paired with a Trane Condenser with sound reducing top XL18i Two Stage Cool with Two stage Compressor model number: 4TTX8060A1000A matched with an all aluminum coil model number: TG86660D210B2722AP, AHRI# 10101906. We install new secondary drain pan with risers and isolation vibration pads to reduce vibration and noise output. New gas flex with sediment trap. We will remove old Smartvent system and install new zone board to accommodate the zone system and install (2) Nest thermostats. We will install new Condenser pad with new electrical disconnect and new whip. Rewrap with UV wrap on the line set per code. We will remove old ductwork and dispose. Install all new ductwork with R8 ductwork sized to exact CFM output for each room to ensure comfort to with in one degree of the thermostat. Install all new wyeâ€™s, collars and perfor
- Cable snake drain line to establish flow - Cable snake with multiple passes to thoroughly clear line - Club Membership - Cable snake drain line to establish flow - Cable snake with multiple passes to thoroughly clear line - Electronic video scan used to confirm sewer/septic line open - Club Membership - Cable snake drain line to establish flow - Cable snake with multiple passes to thoroughly clear line - Electronic video scan used to confirm sewer/septic line open - Locate distribution tank for field leech lines - Replace broken concrete lid for tank - Provide precast concrete lid or poly riser with fiberglass lid plus install - Continue diagnostics and verify distribution tank/leech lines operating - Club Membership - Cable snake drain line to establish flow - Cable snake with multiple passes to thoroughly clear line - Multiple â€œHydro-scrubâ€ using Jetter to clear lines - Electronic video scan used to confirm sewer/septic line open - Locate distribution tank for field leech
Performed diagnostic furnace under house Lincoln. Amana split system on platform system has ecobee tstat, not working found breaker off, turned on and fan runs no heat, error code 6 flashes open rollout. Found unit not passing flame evenly. System needs regular proper maintenance. Figure out what was wrong with system, then test system and run system. System needs burners cleaned, flame sensor cleaned, Pulled and cleaned all 3 burners, and flame sensor just to be safe. Tested system running at this time. If problem consists will need to replace burners. Because of rust.
Install high efficiency 5 Ton Trane system with two stage and variable speed blower in Lincoln Ca. Nest and new Honeywell zone board to be included.
Customer has a bad shower cartridge in his master bathroom shower that is not working, previous plumber could not remove the cartridge because tile was in the way of removal. Customer removed the recommended tile, removed the cartridge and installed the new one. Turned the water on with no leaks, shower works perfectly.
Homeowner in Lincoln Ca, looking at possibly converting from gas to heatpump. Provided options for going back with gas and converting to all electric heatpump.
Flush tankless water heater (Maintenance) - Basic diagnostics include - opening cover - turning unit off and on to verify start up sequence - visual inspection of internal components - Manufacturer recommends water heater flush annually - Turn on water to house to test for leaks - Hot water temperature and fine tuning included - Club membership
Performed a whole home plumbing inspection, upon the inspection i found a few concerning issues. Washer hoses should be replaced with steel braided hose, hall bathroom tub diverter is dumping out water when diverted to the shower.The hall bathroom flapper is being held by a wire, master bathroom toilet needs a complete rebuild. Customer stated the master bathroom tub does not control the temperature correctly, recommend a new tub valve cartridge. The customer decided to wait on repairs, she will contact us when she decides to get these things taken care of.
Performed annual heating maintenance Lincoln. 19 yr old York split Attis yard. Found system tstat without batteries. Turned system on, found filter dirty, 20-24-1. Recommend changing filter more often. Or switching to a washable electrostatic lifetime filter. Unit appears to have repairs done in the past. Checked hot surface ignitor ok, checked blower capacitor ok. Ran system, system running at this time. Turned system off. Come summer need to dive more in-depth on drain pan, and drain lines.
Performed annual heating maintenance loomis. on a 15 yr old York split system, black flex ducts sealed. Found platform dirty, cleaned off unit and platform. Adjusted angle of return duct for better airflow. Opened up unit and found that the door safety switch has been disabled. Checked blower cap ok for now. Cleaned burners and flame sensor. Checked gas pressure ok. Tested system ok for now.
Replaced the flapper in the toilet Water pressure becoming dangerously high 75 psi Possible replacement for Pressure Reducing Valve Customer wants to think it over a bit
Replacing 2 pfister shower cartridge One in the hall bathroom and the second in the guest bathroom. Tested everything is working properly. Also replaced all three toilet flush valve with flappers. Tested found no leaks everything is working homeowner has approved
Install 5 ton High efficiency 2 Stage Heat and 2 stage cool with true variable speed blower Trane split system in Lincoln Ca. Replacing with new R8 ductwork and adding a return with return plenum. Change out Beutler zone board to a Honeywell zone board and do away with their Smartvent. Install 2 Nest thermostats. All permits and title 24 testing will be performed.
- Disconnect drain assembly under sink - Visually inspect findings for lost â€œear ringâ€ - Reassemble after ear ring retrieval - Test drains for leaks by operating