AS ALWAYS GREAT HELP WITH THE ISSUE
Great advice as well as service. All my questions got answered and Scott got my appliance up and running,
Ken, and the team there at Crystal Blue, provided us with a great overall experience with the installation of our new AC unit. Thank you Ken for your honesty, and your follow-up... Great experience!!
Scott did a super job repairing our cooler and he has a great personality.
They did a great job.
Micheal, Justin & Keaton were awesome!! They were very professional, honest, and did an outstanding job!! Very thankful for their efforts!!
i would recommend Sean to anyone. Job well done.
I would now never call anyone else , great investigation work to get at the deep problem not just a quick fix and three months later the same problem .they worked hard to find the real culprit.
Install pressure reducing valve and repair leak in 1â€ water main. Water pressure was at 80 psi and needs to be reduced. Installed 1â€ pressure reducing valve, 1â€ 1/4 turn ball valve and new 3/4â€ hose bib. Also replaced approximately 2.5 feet of 1â€ cooper pipe, a 90 degree bend, a1â€ t, and a 1â€x3/4â€ t. Also installed 1â€ pvc union to irrigation system. Re pressurized water to home to test for leaks, no leaks at this time
#no Reschedule for next week. He was heading out as I got there.
Performed diagnostic on 2nd story roof ac. All parts ok noise is coming from compressor. Compressor not pumping refrigerant correctly. Standing pressures 150/150, running pressures 120/240... and the unit is turning itself on and off. Need to replace compressor quote 3810.01, or condenser we need to send out our comfort advisor.
Cap off existing location were the recirculation pump ties in and tie into the 3/4 line going back up to the hot water system#no we are going to be ordering a mixing valve to replace the one located on top of the water heater, I am not scheduled due to not knowing how far out the part is
Found recirculation line was tied back into the Coldwater feed without a check valve it was allowing hot water to be pushed into the cold water and not back into the water heater. I am returning Friday to install a check valve. Right now the recirculation pump is off and the valves are closed to make sure our diagnosis is proper
Install new 50 gallon natural gas Bradford white water heater with code upgrades including safety drain pan with drain line to exterior of building, gas line debris trap and thermal expansion tank
Building does not have water main shut off valve and one needs to be installed After shutting water main off at city side, disconnected exposed water line and turned water back on to determine direction of water flow. Turned water back off and started connecting building side shut off valve and pressure reducing valve. On site maintenance manager came out to see progress and had him go test to see if water was off to building as ball valve had already been installed with city shut off valve back on. Maintenance manager stated water was on. Water line thought to be service to building is service for sprinkler system. Re assembled pipe with original parts per customer request as work being performed is not what both plumber and maintenance manager thought. Manager is trying to locate building blueprints to give a different quote at a later date. Customer will call back if and when prints are found to give new quote.
#nn Talk to customer informed her that air scrubber is not available anymore had to deal with and fix pricing and issues that was going on with system determine what prices needed to be charge for appropriately there needs to be an $82 credit applied to this invoice last invoice needs to indicate $89 diagnostic for main system $39 diagnostic for mini split system and $82 down payment for this job 8/15/19 Open electronic air filter from manufacture found no power pack electronic air cleaner filter will not operate without power pack appropriately/designed. Will need to come back with power pack and reason for moisture accumulating by returns.
Need to make corrections on install of gas water heater per inspection report. Removed stainless flex line from t&p line and installed rigid 3/4 â€œ copper line. Also extended safety drain pan to exterior of home per inspector, With 1 â€œ pvc. Also found t&p line not extended to side of home. Ran t&p line to exterior of home as well with 1â€ copper. Painted new lines with primer paint per code and strapped to wall. Customer has stated that he will install upper air vent and co2 alarm. No Charge to customer.
Main line backed up access point backyard house in on a hill will run 300 machine and attempt to clear ....cleared line ran camera major root intrusion at top of hill under concrete type of pipe clay thereâ€™s a second root at 79 feet at city tie in to there line. Recommend spot repair at top of property. Would have to jack hammer up concrete in this area customer responsible for replacement
Use special tools to cut out the existing flange and remove a small amount of concrete around the flange to slow the new abs flange to sit flush. Reinstalled toilet tested and found no leaks. 1 yr club membership. This repair has 1 yr warranty
Performed ac maintenance on a 14 yr old gas package unit roof loomis. Changed filter for client with new electrostatic washable filter. Found system al parts in specs. Dual capacitor 45-5 ok. System has hard start kit. Tightened connections on contactor. Checked refrigerant, numbers higher than I would normally expect to see, but gave system a good bath, dragged hose onto second story roof. And numbers didnâ€™t change. So itâ€™s working the best it can now. We will just have to keep tracking them over time to see if anything is going on. Recommend regular maintenance/preventative maintenance on system to track things like refrigerant to see if we have an issue before failure.
Install customer supplied pull out sprayer and install ice maker water supply line. Installed water supply for new fridge ice maker and tested for leaks. Also informed customer about water filtration system and how to maintain. Customer is purchasing new kitchen faucet fixture to be installed on Tuesday August 6 at 10-12 first call. Will collect rest of payment upon completion of work Tuesday. Arrived at 10 am to install customer supplied kitchen sink faucet. Model is Moen 87042srs. Turned on water supply and tested for leaks.
Was able to locate make of shower being a grohe tempress Ii , Sent pictures to the manufacturer should have notifications within 24 hours from the manufacturer. Going to set another phone call ticket up for Wednesday afternoon