Performed diagnostic Loomis. 21 yr old split system. Need to replace dual capacitor to get system to turn on so I can test if anything else is going on. Checked compressor windings weak. Recommend hard start kit to take the load off of the compressor at start up. And regular maintenance to try and lengthen life of system. And recommend annual maintenance.