Performed annual ac maintenance Loomis. Checked refrigerant charge ok. Dual capacitor 55-5 ok, contactor ok. Disconnect ok. All electrical components ok for now. Changed 3 x 12-20-1 filters downstairs. Washed condenser coils with hose. Cycled systems on and off to verify properly functioning. System has 6 supplies and 3 returns. With 18 degree temp split at this time. Drain lines draining correctly out primary at this time. Recommendations, start amps for condenser starting to climb we can add a hard start kit or compressor saver kit to unit to help take the load off of the compressor at start up.