Great customer service and professional work completed. I have used them on multiple occasions and highly recommend.
Was able to schedule same day service. Very profressional, clean and courteous. Gave great recommendations and knew his stuff. Much appreciated!
Kevin was both timely and professional with the replacement of our dead garbage disposal.
I feel like I've found a plumbing company I can trust, and would not hesitate to call them again should the need arise. Sean was knowledgeable and efficient.
Wax ring is leaking and needs to be replaced, disconnect water supply and flange bolts to remove toilet and replace wax ring. Reset toilet and connect water supply and check for leaks Once toilet was removed found that toilet was not equipped with double wax ring to accommodate for new tile floor. Installed new flange bolts, wax with flange and wax extension to accommodate for floor. Reset toilet and tested for leaks, no Eats at this time.
Customer had concerns with leaky kitchen sink faucet. Customer has cleaners on site and they found water under kitchen sink cabinet. Customer found the hose connection for faucet sprayer had come loose and tightened. Customer was wanting verification from plumbing company to verify that there are no other leaks. No leaks at this time, no charge to customer for service today.
No answer at the door.
Water quality, Puronic well unit in meadow Vista ca. Install new defender well unit with a spin down filter ran to the outside New valve and brine tank. Installed 5 bags of salt, tested the unit and found no leaks, showed homeowner how to clean out the spin down filter.
Club membership with tankless flushing test and the unit is Working, also tested water with help of the water purification specialist and found that the current water softener is intermediately working this is why we are showing signs of calcium buildup throughout the house, the unit is from 2011 it is never been serviced and is a unknown model we are going to be returning to replace with a new puronic defender well unit with spin down filter. We are placing the order and are out about 1 week
This is info on the current water softener. Ms32 1 qubic ft Water softener has a fasfate cartridge hardness 11 ga Peters drilling and pump. These notes are mostly for me so I can do research and find info about the current water softener
Found a tankless water heater with the north scale shield set up that filter has not been replaced for eight years, and the tankless water heater has not been flushed. We are returning on Monday between 10 and two so we can install a new skill guard filter and flush the tankless water heater. ( tankless flush is included in club membership)
Customer has begun a remodel on upstairs master bath 4 years ago and needs a quote for plumbing. Customer wants to relocate tub and toilet drains as tub will be facing different direction than original design. Tub flange needs to move 2.5â€ to interior wall to accommodate for code requirements. Customer is building stem wall between tub and shower and will be done by time technician arrives to do plumbing work. Customer will also have floor exposed for technician to do plumbing. Customer will call back to schedule a time for work to be completed.
Lift station pipe is broken under concrete we will reroute line through wall so pipe is not under retaining wall materials will be abs husky bands 45 long sweep 90
Line for power flush toilet is back graded and has a belly causing issues for toilet will have to pull up deck boards to access area to correct issue will also install a clean out to side of deck Repair valve for flushmate toilet
Meadow Vista California heating AC service heating AC maintenance heating AC diagnostic HVAC replacement. Performed AC maintenance bedroom / downstairs unit - turned the unit on to check operation of system turned on / running with no problem. Checked refrigerant pressures good, checked amp draws compressor 7.56 , outdoor fan 1.1 good, capacitors 80/5 reads 82.1/3.9 Condenser fan capacitor out of manufacturers tolerance +/-6% =+/- .3, Visual inspection of electrical - wiring good no burnt or overheated wire connections, Service disconnect wires tight, contactor - contact points normal wear. electrical megaohm test - unit passed. performed simple water wash of condensing coil and flushed condensation drain line part of AC maintenance Unit operating Repair replaced condenser fan capacitor
Meadow Vista, CA, AC heating service AC heating maintenance AC heating diagnostic Perform heating repair for American Standard / Trane 90% furnace Installation of the gas valve will remove old gas valve install new gas valve and set gas pressure to proper pressure per manufacture.
Meadow vista California AC heating service AC heating maintenance ac heating diagnostic. heater not working - diagnostic findings found bad gas valve. Main control board with solder joints breaking and overheating. causing possible intermittent problem or could fail at any time.