Was able to schedule same day service. Very profressional, clean and courteous. Gave great recommendations and knew his stuff. Much appreciated!
Kevin was both timely and professional with the replacement of our dead garbage disposal.
I feel like I've found a plumbing company I can trust, and would not hesitate to call them again should the need arise. Sean was knowledgeable and efficient.
No answer at the door.
Water quality, Puronic well unit in meadow Vista ca. Install new defender well unit with a spin down filter ran to the outside New valve and brine tank. Installed 5 bags of salt, tested the unit and found no leaks, showed homeowner how to clean out the spin down filter.
Club membership with tankless flushing test and the unit is Working, also tested water with help of the water purification specialist and found that the current water softener is intermediately working this is why we are showing signs of calcium buildup throughout the house, the unit is from 2011 it is never been serviced and is a unknown model we are going to be returning to replace with a new puronic defender well unit with spin down filter. We are placing the order and are out about 1 week
This is info on the current water softener. Ms32 1 qubic ft Water softener has a fasfate cartridge hardness 11 ga Peters drilling and pump. These notes are mostly for me so I can do research and find info about the current water softener
Found a tankless water heater with the north scale shield set up that filter has not been replaced for eight years, and the tankless water heater has not been flushed. We are returning on Monday between 10 and two so we can install a new skill guard filter and flush the tankless water heater. ( tankless flush is included in club membership)
Customer has begun a remodel on upstairs master bath 4 years ago and needs a quote for plumbing. Customer wants to relocate tub and toilet drains as tub will be facing different direction than original design. Tub flange needs to move 2.5â€ to interior wall to accommodate for code requirements. Customer is building stem wall between tub and shower and will be done by time technician arrives to do plumbing work. Customer will also have floor exposed for technician to do plumbing. Customer will call back to schedule a time for work to be completed.
Lift station pipe is broken under concrete we will reroute line through wall so pipe is not under retaining wall materials will be abs husky bands 45 long sweep 90
Line for power flush toilet is back graded and has a belly causing issues for toilet will have to pull up deck boards to access area to correct issue will also install a clean out to side of deck Repair valve for flushmate toilet
Meadow Vista California heating AC service heating AC maintenance heating AC diagnostic HVAC replacement. Performed AC maintenance bedroom / downstairs unit - turned the unit on to check operation of system turned on / running with no problem. Checked refrigerant pressures good, checked amp draws compressor 7.56 , outdoor fan 1.1 good, capacitors 80/5 reads 82.1/3.9 Condenser fan capacitor out of manufacturers tolerance +/-6% =+/- .3, Visual inspection of electrical - wiring good no burnt or overheated wire connections, Service disconnect wires tight, contactor - contact points normal wear. electrical megaohm test - unit passed. performed simple water wash of condensing coil and flushed condensation drain line part of AC maintenance Unit operating Repair replaced condenser fan capacitor
Meadow Vista, CA, AC heating service AC heating maintenance AC heating diagnostic Perform heating repair for American Standard / Trane 90% furnace Installation of the gas valve will remove old gas valve install new gas valve and set gas pressure to proper pressure per manufacture.
Meadow vista California AC heating service AC heating maintenance ac heating diagnostic. heater not working - diagnostic findings found bad gas valve. Main control board with solder joints breaking and overheating. causing possible intermittent problem or could fail at any time.
Meadow vista / auburn California AC heating service AC heating maintenance AC heating diagnostic Main living unit Performed heating maintenance inspection of the electrical found small chew marks on thermostat wire caused by rodent. inspection of control system in furnace shows wear possible failure or intermittent problems may be caused from this. if this occurs recommend replacement of control board. Tested amp draws (good), Flame sensor start up 2.9 running 2.9 (good) Burners clean, Heater safeties good, Gas pressure 3.53 adjusted to mfg. specs of 3.50 , ohms reading of hot surface igniter 66.8 no wear visible on ignitor. blower motor capacitor 10 reads 9.2 allowable tolerance for capacitor +\-6% = .6 capacitor out of manufactures tolerance. recommend replacement of capacitor. system working only recommended repairs needed at this time to help prevent more expensive repairs to system. air filter good. Visual inspection of ductwork good no broken or disconnected ducts Bedrooms
Replace Sloan flush mate for wall mount toilet American standard also replaced tank bowls the old ones were worn out due to age I believe the tank installed by other company was used and never functioned tested new unit and works great