Outstanding!! Thank you so much for your services. I've kept your business card on hand and we will definitely call you if we have any issues having to do with our plumbing many thanks again.
ON TIME,,FAST AND KNOWLEDGEABLE.....
Today we took a look at a leaking faucet in the downstairs bathroom for customer I did a quick diagnosis On the Delta cartridge on the cold side cartridge seems to be in good shape so I went over meaning of options for the customer and She has decided to possibly purchase a faucet and have us come install it at a later date. We look forward to servicing this customer in the future if she seem to be happy and satisfied with the job performed.
This estimate is to run a drain snake through upstairs shower to attempt to clear drain
Estimates given, crawled under house, another plumbing company out, second opinion. Notice abs wye was backwards and branch lead to septic and the straight lead to the dead end hold water. Tub is also plumbed in incorrect vent below drain upon further inspection put a level on the rest of sewer line toward back bathroom. Line started flat and that at bathroom before connection at toilet back graded. Stated customer of issues and left estimates
Shut down water at house and drain system. Install two outside 1/2â€ hose bibs. Turn water back on to house and check for leaks. Clean work space. Installed hose bibs and checked for leaks. Emailed invoice to customer.
Plumbing repair. Toilet leaking. Nevada City
Nevada City tankless water heater diagnostic estimated for replacement
Plumbing Nevada City. Nevada City Plumbing. Estimate trenchless pipe install.
Plumbing Nevada City commercial. Troubleshoot existing 300 gallon natural gas water heater.
Plumbing Nevada City shower installation Kohler shower repairs water heater installation Toto toilet installation
whole House Repipe, re plumb house, pipe repairs, pipe leaks, plumbing services