Performed ac diagnostic, found unit in off position had client turn on unit. Unit cycled on, turned off unit at disconnect. Tested dual capacitor and blower capacitor. Let system run 30 min and fan just started slowing down and stopped. Needs new outdoor fan motor, 1/4 horse 1100rpm 240v. Scheduling to come out to tomorrow. Whenever we can squeeze it in, client prepaid.