Sean was able to diagnose our Tankless water heater problem and get the parts ordered and on there way fast with little down time.
#no We will remove old equipment per EPA regulations and install a complete new Hvac system plus ductwork. New plenum plus ducts, collars, y connections and running all new R-8 ducts. New Coleman 90k BTUH Downflow furnace and install new 3 ton condenser and coil. Cut in new return and relocate one supply register. New electrical disconnect, whip and breakers. New condenser pad, txv and install a Refrigerant line set to condenser, run under home.
Install thermostat couple and clean burn chamber in old GE water heater. Installed 18 inch thermogenerator and cleaned burn chamber of foreign debris. Turned gas back on to check operation of water heater, heater is working fine.
1 1/4 main feed to house has no prv will install new valve and prv tested good no leaks
Replace six price Pfister cartridges 4 in the master bath and 2 in the guest bath. Install new pop up assembly in master bath left hand sink and tub spout nipple in hall bath , club membership. Tested and found no more leaks, homeowner is happy
We are returning Wednesday afternoon to install the proper brass cartridges in the hall and master bath lavatory sinks, new pop up assembly under master left side sink and nipple for tub spout pp cartridge # st1280x
Install new p trap assembly and brass male trap adaptor. Customer removed old trap assembly for repair but could not find proper parts. Gave quote to replace p trap assembly from wall to sink . Ran sink faucet to test for leaks, no leaks at this time.
Orangevale CA. Replaced Delta cartridge in master bath and new toilet flapper also in master bath tested and everything is properly working, showed homeowner and they are satisfied
Put 2 x 4 block behind the water heater to help secure it and cut existing temperature will be fine to be 6 inches above the concrete.
Grohe parts customer will acquire warranty parts and call back
Toilet backs up sometimes and customer is able to plunge it clear will. Auger toilet to determine if thereâ€™s a foreign object in it. Ran camera from clean out thereâ€™s a belly in the main line sewer at the tie in causing toilet to back up recommmend spot repair house is on slab and customer does not want to jack hammer up house. Alternative would be to install a power flush toilet.
Orangevale main line sewer blockage #nn customer had septic exposed for us to run main line sewer with 300 machine minor roots causing slow drainage tested everything we have good flow
Blocked drainage line, hydrojet is only way to clear line, snake no efficient enough to remove debris.
Sanitary tee is broken on the grey water side thereâ€™s also a root in exit pipe will determine how much when it is excavated will replace broken pipe with abs fittings and 4 inch abs pipe. Repair on sanitary tee at exit point for grey water side excavated 3ft down the side of tank exposed connection at concrete wall. Replace section with abs pipe and fitting packed wall with concrete to seal up fitting and pipe coming through wall sent pictures to Jeff at Advanced Septic for inspection report.
Install Navien supplied wire harness and thermistor warranty parts replaced harness tested works great
Warranty service error code 421 Navien sending wire harness to shop