Performed tune up maintenance contract. Turned system on from thermostat and unit kicked right on. Started at indoor unit. Inspected unit for cleanliness and proper operation. Inspected all electrical connections. Inspected blower motor and capacitor. Motor pulling 5.67 amps Blower wheel is clean. Filter is clean. Condensate is draining properly. Have a 20 degree temperature split. Unit is operating at this time. Inspected condenser. Inspected unit for cleanliness and proper operation. Inspected compressor, have a amp draw of 13 amps Condenser fan motor pulling 1.7 out of 1.4 This is over amping the motor. Capacitor is 45/7.5 and is out of spec causing the high amp draw. Contactor is heavily pitted and burnt, causing high resistance throughout the circuit. Client approved replacement of capacitor and contactor. Fan motor is now pulling 1.4 witch is still at peak but not over amping. System is operating at this time.