The technician was timely, friendly and great at explaining things in detail.
Customer stated blower motor stoped working, Tested capacitor and it was out of spec, replaced for testing and motor would spin slowly but not at full speed, tested motor and have a high resistance, have high voltage and control power to the motor, Will need to replace the motor and capacitor, thermostat wire is exposed and chewed up, need to run new wire and insulate. Contactor is heavily pitted and burnt, suggest club membership, Customer approved all work. Perform work Tomorrow.
Pilot Hill California HVAC Service AC heating installation AC heating diagnostic trane gas-fired propane furnace installation of new control board removal of old part and install new control board. removal of in-line damper and installation of external wall damper.
Replacement of 7" stove exhaust damber. If both repairs are done at the same time, no trip charge. If done at separate times $45 tri charge will be added.
Tankless water heater. Pilot hill plumbing. Pilot hill.