Performed ac diagnostic found system off and tripped far right 40 amp ac breaker. Zinsco 40 amp 2 pole wide. Breaker also not a correct breaker, no lock between poles. So one leg can trip on its own. Tightened both power wires both wires where able to be tightened. If problem happens again, will need to replace breaker.