This will be to remove harmful exhaust gases from gas producing stove as well as moisture and gases from bathrooms to outside. Install new roof cap vent for stove 6 inch will have to extend duct from stove exhaust up to new roof jack. other work will be for bathroom exhaust fans will need to extend and run 4â€ duct venting to roof jacks as well.
Duct test past, had to charge system to manufacture specifications for refrigerant test to pass (passed) Cal Certs down cannot print paperwork duct test company will email paperwork. will need to send results to customer either email form and have them print or print and send to customer for city inspection.
Customer needs to talk to family before making date for quoted repairs as she just had us install new HVAC system. Customer will call to schedule an appointment.
Install 5 ton American Standard True variable speed blower, two stage heat two stage cool. Replaced all the ductwork with R-8 insulated ducts, all ductwork materials included in this proposal. Will need supply and return plenums. Add (2) extra returns to home. Size to be determined upon walk thru. Add extra supply run to kitchen. Nest 3rd gen learning thermostat. Run new control wire for thermostat and condenser if needed. New condenser pad. Title 24 duct tested and permitted.
See notes for material. Reviewed
Install 5 Ton American Standard Two Stage Heat and Two Stage Cool with True Variable Speed Blower. Replace all ducts with R-8 ducts, add (2) extra returns Supply and return plenum needed Add supply to kitchen New flue pipe and roof jack needed Drain pan needed Electrical disconnect and whip with new pig tail New control wire for thermostat and condenser Nest thermostat 2 year crystal Blue Club
Estimate for bath remodel
Rio Linda California heating AC service AC maintenance AC diagnostic residential and commercial hvac equipment. Trane 3.5 ton split system Diagnostic AC system running visual inspection condenser coil plugged solid. restricting airflow causing system to run hot and overheat. inspection of system found refrigerant charge low. most likely caused from refrigerant leak. Repairs for system to operate chemically cleaned condenser coil. charge system with our 22 refrigerant. Recommend performing leak search to determine cause of leak and fix appropriately. Due to type of refrigerant in the system and age of unit other option is adding sealant to system to try and seal refrigerant leak sealant is not a guarantee. Repairs for AC system completed at this time Chemically cleaned condenser coil and charge system to manufacture specifications. Added system sealant to system and dye if sealant doesn't work we'll be able to come back at a later time and look for leak.
Install 3 electric heaters 2 - 72" units dinning room and second bedroom, 1 unit in bathroom. Insulation includes part, shipping miscellaneous material and labor to install Warranty one year parts and labor for normal use New units will have internal safeties for overheating protection will be safer to run
Maintenance 9 electric baseboard heaters Hall way unit Cadet mfg. 48" m#4F1000 240v Cleaned, thermostat working, wire Connections tight found no problems Middle bedroom unit Pacific baseboard heater 72" model 15bg6 240v Cleaned unit, no power to unit turned on Breaker tested unit it is operating at this time is an older unit only has thermostat switch just has off and low through high setting (always on) doesn't have safety switches either could overheat /short out cause electrical problems Kitchen 15bg6 240v Cleaned unit, inspected for proper operation, thermostat working wire connections tight no problems at this time Living room two units both 20bg8 Cleaned both units tested for normal operation. both units controlled by one thermostat. Neither unit came on inspected electrical wiring found units have been disconnected inside unit that has thermostat. Soot build up due to electrical issue (smoke/fire-overheating) quick diagnostic found power supply to units only 115 volt and
Rio Linda California heating AC Service Repair Lennox gas package unit on roof install rain flashing properly to divert rain , replace broken drain pan and install drain line
Heat exchanger failed, replaced user manufacturer warranty. Rio linda, ca Heater repairs
Rio linda tankless not working. Did a plumbing service and got it to function.
Rio linda instalation of two Kohler toilets and repair on a third toilet
Rio Linda A/c unit not running. Replaced capacitor and working great.