honest and very caring to my financial situation. Went above and beyond to help me.
Very professional and quick!
Wonderful as always
Ken was honest, sympathetic for my circumstances and straight to the facts. I appreciated the "no pressure" and liked the estimate of cost.
I have been using Crystal Blue for several years ever since I was the 'victim' of a holiday weekend water heater emergency. I have continued to do business with them because they are honest, professional, courteous, and good at what they do, and very competitively priced!! No different this time. Their tech, Michael, was all of the above and then some. He took nearly two hours to discuss my situation, do a thorough inspection of my current system and my needs, etc. By the time he was done he provided me with five (yes five!!) detailed options, which included two highly rated manufacturers, and explained the differences between each. He answered all of my questions, took detailed note and photos, and even called the manufacturers to confirm specs. I also got bids from several other "well known" HVAC contractors. I had done my homework, even went to the Sac Home Show and spoke to several contractors there (some of whom also later provided me with estimates). Bottom line... Crystal Blue was by far the best experience and estimate. As with past Crystal Blue experiences, Michael was GREAT!
We use Crystal Blue for all our plumbing jobs.
The Plumbers did an excellent job fixing the pipes, even under difficult circumstances. We are very happy with Crystal Blue's work.
Tom was awesome! Super nice, quick, cleared clog. A++ Will be contacting for future work.
Guest hall bathroom Toto toilet not filling. Install new fill valve and flapper. Adjust water levels in upper tank and test operation. Installed new fluidmaster 400 a fill valve and Toto brand low flow flapper. Tested operation. Toilet works like new, no issues at this time.
12j18 Lennox part number bolt on txv. 2 ton
Rheem 50 gallon water has a failed gas sensor valve #no will replace and relite unit . Thereâ€™s a procedure to reset control valve set to off turn dial to lowest setting turn unit on and turn heat setting from low to high 7 times to reset gas control valve to clear error code. Unit is now operational.
Performed ac tune up Rocklin. 1 yr Goodman split system. Filters ok, 20-30-1 and 14-14-1. Checked electrical connections all tight and ok. System needed a bath due to construction dust and dirt. Washed coils to help with Efficiency. Tested all parts ok. Refrigerant ok. New system just need to keep up on filter changes. System looks good. 18 degree temp split.
Rocklin California AC heating service maintenance diagnostic Performed AC maintenance - turned the unit on to check operation of system turned on / running with no problem. Checked refrigerant pressures good, checked amp draws compressor 9.8 , outdoor fan 1.13 good, capacitors 50/5 reads 46.6/5 Good within manufacturers tolerance +/-6%, Visual inspection of electrical - wiring good no burnt or overheated wire connections, Service disconnect found loose wire connections tightened as part of AC maintenance, contactor - contact points slightly pitting and burnt not affecting function / normal wear. electrical megaohm test - unit passed. performed simple water wash of condensing coil and flushed condensation drain line part of AC maintenance Unit operating with no problems at this time.
Customer was informed by Rocklin that they have high water usage. Isolated the main feed meter is spinning will have to call for leak detection thereâ€™s no visible signs of a leak above ground. Found a control valve in landscaping that is not shutting down will replace and retest.
Replacing the bearing x2, which means removing the old rusted on bearings from the shaft then getting the new ones to go in place. Replacing the pads x4, which is removing all the doors and removing the old falling apart pads, and replacing them with new more efficient ones And renewing the service maintenance plan Client will pay like he always does. Bill to
Performed diagnostic found that Swamp cooler has destroyed bearing. Need to replace bearing to fix system. Also recommend replacing the water pads at the same time. Need to find motor bearing for unit. See pictures. System has 2 bearing, we should replace, both... also all 4 pads are in rough shape recommend replacing those as well. Took down model information will call tomorrow morning with price and availability once we know more. Client needs it ASAP Recommend resigning back up on the commercial pro plan.
PO for this job is R39407 Pump down system. Remove old coil. Replace coil with new coil. Re braze in new coil, pressure test system with nitrogen, vacuum system, and then factory charge system. Clear partially clogged drain lines. Job completed August 13, 2019
#no. Unable to move forward
Hydro jet all accessible lines from clean out due to heavy build up of grease secondary lines are backed up cleaned out secondary lines and ran the camera lines all clean out to main tie in.
Install new gas Bradford white 40 gallon water heater with water heater pan, expansion tank, supply lines, gas valve, earthquake straps, removal and disposal of old water heater. Tied the drain pan into the existing 1in pvc in the floor . I was told by Michael at our office but this is a billable customer did not collect
Performed diagnostic on 31 yr heat pump split attic side yard. Found system holding refrigerant for now. Found system cooling master bathroom just not anywhere else. Found system running heat strips at the same time as the ac... removed wire to heat strips to stop the system from fighting itself and system is cooling at this time. Tested heat working well stopped it when system was producing 90 degree air after only a few mins. Signing up for the maintenance plan for a years worth of maintenance since this system has not been properly maintainedl
Customer is providing parts for us to install . Recirc pump a crossover valve .gas cock valve and supply relite water heater turned on gas and water no leaks