A nice experience and educational!!
Great dude, knew his stuff. Great work and meticulous from start to finish.
Came on time and was clean service.
Awesome professional top quality!
Completed wall unit tune up, Inspected unit for cleanliness and proper operation, Filters where clean, evap coil has a little dust build up, Unit has a proper temperature split, system cycled on like it should, system is operating at this time.
Performed tune up maintenance contract. Turned system on from thermostat and unit kicked right on. Started at indoor unit. Inspected unit for cleanliness and proper operation. Inspected all electrical connections. Inspected blower motor and capacitor. Motor pulling 5.8 amps Blower wheel is clean. Filter is clean Condensate is draining properly. Have a 16 degree temperature split. Unit is operating at this time. Inspected condenser. Inspected unit for cleanliness and proper operation. Inspected compressor, have a amp draw of 12.69 Condenser fan motor pulling .78 Capacitor tested within spec, Contactor is heavily pitted and burnt, Your contactor is the gate way of power to your unit, When they start to burn like this a high amount of resistance is caused, witch gives a improper amount Of power to both of the motors at your unit. I highly suggest that the contactor be replacing to ensure a long life of the unit. System is operating at this time.
Perform plumbing inspection found kitchen faucet sprayer to be cracked other than that angle stops were aged but everything was in working order did not find any leaks Will email over report with photos and comments on issues that were found.
Out to estimate replacement of 51 y/o 4 ton gas/electric split system. Upflow furnace in closet. Client not ready to make decision at this time. Leaning towards repair option Drew left.
Client stated fan blade ripped off. Verified customerâ€™s concerns. Found one blade on fan to be torn in half. This unit and company is not longer in business so parts are hard to find. Client also stated before this happened the unit would only get down to the low 80s in the home on a hot day, R22 system. The replacement of the fan would only give me the ability to get the unit running and test to see if there are any other issues with the system. Pulled power so no further damage can happen. Having our comfort advisor come out today to go over replacing the system as a hole Fan replacement with labor would be $350 Paid $89 for diag. System is not operating at this time
Performed inspection filled out inspection form will email to customer found some recommendations all estimates are included in the attached email
Phone call about gas estimate
Upon arrival customer would like video inspection for the house. I Searched for to a clean out was an able to find a clean out went underneath the house found a fitting that had a jim cap where I can access to line this estimate is to camera line from underneath the house record video and email it to customer
Clear kitchen sink clog In this estimate we will need to access the clean out for the kitchen sink if we are unable to access the clean out there will be an additional charge to disassemble the waste line and waste arm underneath the sink to insert a cable down the waste pipe. Once we have disconnected the waste we can then start to send a cable down depending on where the sewer main is we will cable down the branch arm and see if we can catch the clog within the branch arm. After sending the cable down I could feel a clog and had to fight through it push the cable machine to the end of the cable which is roughly 50 feet. Then I ran water for over 10 minutes to ensure that we pushed through the clock and cleared the line. Customer is very happy and satisfied with the job Performed.
Upon arrival customer wanted estimates to install gas line for fireplace estimates are attached an email
This estimate is to auger toilet to remove blockage Will use the toilet auger to remove blockage blockage was approximately 4 feet in after blockages clear, we cleaned toilet for customer,clean toilet of residual debris tested toilet multiple times and flushed toilet paper. the toilet auger successfully restore flow we also tighten down tank bolts a little to keep tank for rocking.
upon arrival found unit not turning on inspected unit for power unit has high-voltage power checked low-voltage power no low-voltage power. checked components that would create low-voltage power found transformer burned up. replace transformer added low-voltage fuse to protect new transformer from burning up. turned system on system turned on and ran for less than five minutes and popped fuse indicating intermittent or high amp short. Performed low-voltage inspection at air handler checked all connections, checked heat strips found no problems at handler. inspected condenser checked low voltage at contactor no problems, low-voltage wiring no problems, checked reversing valve low-voltage no problems. inspected low-voltage wiring in between air handler and condenser found damage underneath line set cover caused by rodents replaced low-voltage wiring Sealed line set cover to help prevent any other rodent damage coming from outside. If rodents exist in at
Customer is looking to add a gas line to the property for a heating unit or a swimming pool. The dynamics on the swimming pool says we could run a three-quarter inch line within 50 feet this rain is going to be 40 feet of black steel wear it well then go underground in transition to poly pipe and we will have an 85 foot poly run. The specs for the heater on the swimming for 120,000 BTU. This means we are going to run a 1 inch gas line from the manifold in the attic to the heating unit itself. If for some reason the house is running on too many BTUs to use the manifold we can then Run a dedicated line off the meter which would be about 45 feet of black steel before transitioning to poly.
Vent is not connected to roof jack and is dumping into the roof. Will need to pull roof jack and re pipe the dryer vent into the attic and re connect Aug 24 repaired dryer vent and cleaned master blower wheel
In this estimate we will need to use special tile cutting bits to drill holes for mollies and screws to install grab bars one in each shower. Also the customer has a delta showerhead that needs to be installed. Then we will need to get an inch and a half hose connection for sub pump down below house.