Ryan was terrific! Even when he found out that he didn't have the parts needed because my project instructions were not conveyed to the installer. I ended up driving to the parts store while he started. Probably should have installed it myself after I factored in the overall price.
Install new badger 5 in sink erator Installed new Badger 5 in sink erator and re routed j bend assembly for proper flow. Tested for leaks and operation, disposal and drain are working normal. Flat rate parts and labor with 6 month guarantee on labor only.
Install new kitchen sink faucet Kohler model number 10433-US-EL brushed chrome finish, single handle. Removed old faucet and left on site per customer request. Turned water back on to faucet and tested for leaks, no leaks.
Install customer supplied whole house water softner
Install new customer supplied kitchen sink faucet, customer is purchasing faucet on line and technician needs to pick up part for customer before install.
Customer is selling home and had some issues that needed to be addressed in accordance with inspection report. Water heater t&p line was running up hill to wall, per inspection report line has been ran in hard pipe and is directed at floor. Gas line for package HVAC unit had flexible gas line penetrating through wall. Ran black iron hard pipe through wall with debris trap in location per inspection report. Customer also had kitchen sink faucet leaking from pull out spray hose. Customer purchased new kitchen sink faucet for install. Customer is also purchasing new water softner for home to be installed on tues the 30th of July. Have provided customer with quote for customer supplied part install. Water pressure checked at farthest water supply from well pump, water pressure is currently at 58 psi(nominal). Will test water pressure once new water softner is installed.
2006 state select water heater not staying lite and leaking from base and needs to be replaced. Water heater also has some code issues that need to be addressed. Quote is flat rate parts and labor and is good for three months. Customer has also been informed of financing.
Kitchen sink faucet, light water heater, change water filter Moen kitchen sink faucet was detached from base stem, re assembled stem and remounted faucet. Checked for leaks and operation, no issues at this time. Re lite water heater and checked operation, water heater is working fine. Customer had new filter for whole house water filter, changed and showed customer how to perform herself. Also showed how to use thermostat for HVAC system. Went to main house and turned water on to water closet in laundry/mud room. Everything in good working order.
Provided estimate for prv customer will call for schedule
Customer was digging hole and rock fell on 1 1/4 â€œ pvc main right next to two conduits. Need to cut pipe out and get repair coupling to fix. Also customer supplied parts for hose Bibb off the main
Had too cut out cabinet to install sink in garage cabinet, install faucet and water and drain supply
Drain clearing no cleanout pull toilet, clear through vent, cleared line installed new cleanout in f