Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Looked at ductwork in basement and return in the house Some walls we moved -return drop only pulling back 1000 cfms I took a lot of pictures and will lay it it to get move air back to system to lower the static This will help but will resolve all the airflow issues . Will call customer next week with quote.
Check hp system ; found lack of return ductwork for a 5tons unit. Only pulling back 3.2 tons of air needs 5 tons of air - static 1.2 New heat-pump/return drop 20/12 - customer said some return were taken out also.