Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Returned to site to install new Draft Inducer Motor. Turned power supply off and disconnected and removed Motor. Installed new Gasket and mounted new Draft Inducer Motor. Completed Wiring connections. Put system back in operation and performed Combustion Analysis on unit. Measured Amp Draw at 2.4 Amps on Inducer Motor. Combustion Readings were within standards. Replaced 18x30x1 Air Filter for unit. Measured Supply air at 121 Degrees with a 71 Degree Return air temperature. As per homeowners request, turned space heater in mechanical room to setting #2. Reviewed hot water heater options with homeowner. Performed Precision Heating Tune Up on Lennox Gas Fired Furnace. Inspected 18x30x1 Air Filter. Homeowner is going to purchase new Filters and replace. Recommend using a pleated Air Filter that does not exceed MERV-8 Rating. Cleaned Furnace drain lines and tubing. Inspected Burners and Heat Exchanger. Tested electrical components on Furnace. While testing system found Inducer Motor was m