Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision AC Tune Up on system. Checked 18x30x1 Air Filter. Filter is starting to get dirty and should be replaced before the summer season. Did not have that size filter on the truck. Need to schedule a time to come back to replace the Air Filter. Checked electrical components on System and found the Capacitor for the Condenser Fan Motor was leaking oil and Eppsâ€™s testing below rating. Replaced Capacitor and tested. Cleaned drain Line for Air Conditioner. Put system in operation and measured refrigerant charge and Air Temperatures. Homeowner stated that the new Water Heater is running out of hot water when she takes a shower after about ten minutes, which is how the old water heater ran also. Checked both thermostats on the water heater which were set to Hot. Ran hot water at the kitchen faucet which was reading between 116 Degrees and 124 Degrees. Measured Amp Draw on Heating Elements at 17.8 Amps. The water heater is operating normally at this time. Homeowner is going