Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Chris was very professional and efficient. He took the time to be thorough and took all safety precautions. I feel confident that the work was done properly, and will definitely call DiBiase again for any future work!
Chris from DiBiase was professional and courteous. In this time of Covid, he was careful to wear covers on his shoes, gloves and a secure face mask which made me feel comfortable with his entering my home to do the work. He was also careful to put things back exactly where I had them and clean up afterwards also. The work was done efficiently and correctly. I will definitely use Di Biase’s services again and would highly recommend them!
Technician was very professional , clean, and courteous. Came when expected, did a very good job, and exceeded my expectations. Would highly recommend!
DiBiase is a pleasure to work with. The work was done completely and efficiently- and clean also. Chris was friendly, helpful, and professional. I would recommend this company highly and will call them again!
Performed AC Tune Up on system. Replaced the 16x20x1 Air Filter. Cleaned Drain Line and tested electrical components on Indoor and Outdoor Units. Capacitor for the Outdoor unit is testing within range, but is getting close to the lower end of its rating on the Fan Side. Put system into operation and measured refrigerant charge and Air Temperature readings on system.
Performed precision heat tune up on Goodman 80% gas furnace. Replaced very dirty 16x20x1 air filter. Duct work is full of dirt and debris, would recommend getting duct work cleaned. Tested capacitor. Checked all electrical conections and components. Checked temperature rise. Tested gas pressure. Cycled thermostat. Gas furnace is working fine at time of inspection. System does not currently have a/c, a/c could possibly be added on.
Performed Precision AC Tune Up on system. Replaced 16x20x1 Air Filter. Cleaned Condensation Drain Line on system. Inspected electrical components on indoor and outdoor units. Inspected Indoor and Outdoor Coils. Measured refrigerant charge on system. While performing tune up, found the Air Scrubber was not operating. Recommend replacement of the Cell Membrane for the Air Scrubber. System operating to standards at this time.
Performed Precision AC Tune Up on System. Replaced 16x20x1 Air Filter. Inspected Electrical Components on Indoor and Outdoor Units. Cleared Condensation Drain Pipe. Would recommend installing an EZ Trap to better clean the Drain Line. The EZ Trap would be wired to the system and if the Drain line clogged and tripped the Float Switch inside the EZ Trap it would shut power off to the system. Measured Refrigerant Charge on system. Refrigerant Pressures are fluctuating due to possible moisture and/or non-condensible in the system. System is cooling and refrigerant levels are within safe operating range.
Performed Precision Air Conditioning Tune Up on system. Replaced 16x20x1 Air Filter. Checked Electrical Components of system. Cleared Condensation Drain Pipe using a C02 Cartridge. Poured Water through Drain Line to ensure it was flowing properly. Measured Refrigerant Levels of system. Homeowner not home at time of job completion.