Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Technician was very professional , clean, and courteous. Came when expected, did a very good job, and exceeded my expectations. Would highly recommend!
DiBiase is a pleasure to work with. The work was done completely and efficiently- and clean also. Chris was friendly, helpful, and professional. I would recommend this company highly and will call them again!
Performed Precision AC Tune Up on System. Replaced 16x20x1 Air Filter. Inspected Electrical Components on Indoor and Outdoor Units. Cleared Condensation Drain Pipe. Would recommend installing an EZ Trap to better clean the Drain Line. The EZ Trap would be wired to the system and if the Drain line clogged and tripped the Float Switch inside the EZ Trap it would shut power off to the system. Measured Refrigerant Charge on system. Refrigerant Pressures are fluctuating due to possible moisture and/or non-condensible in the system. System is cooling and refrigerant levels are within safe operating range.
Performed Precision Air Conditioning Tune Up on system. Replaced 16x20x1 Air Filter. Checked Electrical Components of system. Cleared Condensation Drain Pipe using a C02 Cartridge. Poured Water through Drain Line to ensure it was flowing properly. Measured Refrigerant Levels of system. Homeowner not home at time of job completion.