Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Quality Assurance on American Standard AC system. Homeowner stated that she was having an issue with the AC because she wasnâ€™t sure how to set the Thermostat for the correct temperature. I tested system and measured a 18 Degree Temperature Split. Measured refrigerant charge and added 4 oz of 410-A to increase Subcooling from 3 Degrees to 7.5-8 Degrees. Completed Checklist Form in system and reviewed installation with homeowner. This Installation passed the QA Inspection.