Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
System was running with good numbers when I arrived. Capacitors and electric good. 23F temp split measured between plenum/drop. 3F superheat. Checked filter. Completed AC service Form. Provided estimate to replace Piston and to replace Piston with a TXV. System is operating ok at the time of this service. Homeowners became plan members.