Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Found water inside auxiliary pan, customer stated system has Itâ€™s been shutting off on wet switchAnd can hear water dripping from the back of the air handler, inspect drain, draining ok, inspect coil pan, noticed 3/4 drain is connected to secondary auxiliary port, added 1 gallon of water into pan and noticed starting to drip behind air handler and back of coil. Removed 3/4 plug from primary drain and found clogged port, water is backing into pan, and dripping behind unit, connected drain line to primary port and plugged secondary port, flushed drain with 2 gallons of water did not see any dripping behind unit, told customer to keep an eye on unit it problem continues to happen, we need to pull out coil to inspect pan for cracks, we might have enough slack on line set we will try disconnect coil without cutting line set, two men will be needed.