Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
We have used DiBiase for 7-8 years and highly recommend them.
Tech was excellent! Fast, efficient and extremely friendly. Always happy to use Dibiase HVAC for these reasons.
Performed ac check up attic unit, check electrical low and high flushed drain test pump ok split ok outdoor unit 410 pressures ok capacitor and contactor ok cleaned outdoor coil cycle unit ok
Water leak, found 3 to 2 in reducer leaking on of the joints, will need to replce 3 to 2 in reducer and also will need a 2 in coupler, during testing noticed insid heater cabinet getting hotter than normal, start heater and defrost combustion test with blower on and off, co went over 100 with blower on when blower off goes down to 10, remove limit and inspect ex charger not visual propblem, but you can see flame/light from inside limit, heater should not be runninglike that, turned gas off and electrical, explained customer about situation, once I leave is up to customer to turn heater back on, quote for new exchanger recommend new heater
Performed Precision Air Conditioning Tune Up on system. Changed both Air Filters, supplied by Customer. Please were dirty and blocking Air Flow. Please Check Air Filters every 30-60 Days and change as necessary. Cleaned Condensation Drain Pump and Drain Line. Found Drain Line was clogged and not draining properly causing water to overflow into the Auxilary Drain Pan underneath the Air Handler. Cleaned water and unclogged Drain Line. Tested Electrical Components on Indoor and Outdoor Units. Measured Refrigerant Charge on system. Recommend the Service Membership Program which Includes one AC and one Heat Tune Up annually. Please see attached Estimate.
Just stopping for a second, or fifteen, to enjoy this beautiful sunset view across the farmland.
Replacing this old Contactor on a Payne Heat Pump System in Cochranville. The pads on this Contactor are worn and pitted, which could cause it to not work properly and eventually cause issues with the Heat Pump.