Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Precision Heating Tune Up on Gas Fired Goodman Furnace. Replaced High Efficiency 401 Air Filter. Cleaned Drain Lines and Inducer Hoses. Inspected and tested electrical components. Inspected Burners and Heat Exchanger. Burners are starting to rust and rust is present in heat exchanger. Performed Combustion Analysis on Furnace and measured Air Temperature readings. Installed a Honeywell T4 Digital Programmable thermostat. Programmed for system and tested operation. There is no Shut Off switch at the Furnace to disconnect the power supply and the Breaker Panel is not labeled. For servicing and in an emergency there is no accessible way to shut the unit off. Would recommend installing a Shut Off Switch at the Furnace. Also noted that the Exhaust Vent piping is leaking onto the top of the Furnace. This is rusting the top of Furnace and could cause further issues if it starts leaking into the Furnace Cabinets. Would recommend cutting the 3â€ Exhaust Pipe and adding a new sectio