Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Found supply temperature of 54 and suction pressure 66F(outdoor dry bulb temperature 68F) during maintenance. These are indications of a leak. Thoroughly searched for leaks. Found leak using electronic leak detector at capillary tube at bottom left of evaporator coil. Onfirmed with bubble test. Comfort Consultation is scheduled for system replacement. Collected for plan renewal.