Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Plan member AC maintenance for 3 Ton System: Replaced 20x20x1 Filter Measured temperature split and static pressure. Checked wiring, controls, electric motors and components. Both indoor and outdoor coils are in good condition. Checked refrigerant pressures and diagnostics. Water softness/hardness test Results: 20 gpg CaCO3>> Very Hard. Provided (2) Estimates. 1 for NOVO Water Softener 1 For Water Softener and Filtration System. Air conditioner is operating well at the time of this maintenance.