Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Arrived to do maintenanceâ€™s on two ac units one on right side basement, other on left side of basement. Went ahead and started in the right side, started system, tested thermostat for operation, checked temperature split, checked filter which was still good, checked fan motor amp draw system was running, then shut off. Found system to have shut off on high pressure. Went out and checked error codes found multiple but most were related to the fan not running and causing high pressure and temperature as well as high inverter temperature. Cycled system and fan came on and ran until house had satisfied without faults again. Followed directions to check the fan to make sure it is working correctly and everything is working correctly at this time. Compressor amp draw, condenser fan motor amp draw, and refrigerant pressures all were good Left side of house, checked thermostat for operation, checked temperature split checked blower motor amp draw, checked compressor amp draw, checked refr