Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Chris has been to my house several times for maintenance and repairs as needed. He is always courteous, friendly and a great worker.
During this covid time, felt safe with Chris here maintaining all precautions necessary.
Chris has been servicing my heater for a couple of years now. He is very courteous and explains everything in a way I understand. He is a great representative for the company.
Chris has been coming for servicing my heater and air conditioning. He is very friendly and explains everything so I can understand. He is an asset to your company.
Chris is friendly and courteous. Willing to answer any questions I had. Explained everything he did.
Chris is very courteous and answered all my questions. Even though he arrived later in the day, but within the time I was told, he was very thorough and found the reason for me not having heat.
Performed cooling maintenance, checked air filters ok. Inspected cooling coils and drains. Checked voltage, amperage and electrical connections, measured capacitor values. Started heat pump, checked refrigerant charge and temperature drop across coils.
Tuesday 12/8: Returned to site to replace Flue Piping. Disconnected and removed existing Flue Pipe. Cleaned Out wall termination and Boiler Exhaust Outlet. Installed new 3â€ - 26 Gauge Flue Piping. Sealed all connections and wall penetration with High Heat Silicone. Sealed around outside termination with Silicone. Put system in operation and performed a combustion Analysis to ensure proper operation. Monday 12/7: Performed Precision Heating Tune Up on Gas Boiler. Removed and cleaned Burners and Flame SpAssembly. Inspected Heat Exchanger with burners removed. Relit Pilot flame and checked flame quality. Inspected Electrical Components on Boiler. Flue Pipe on boiler is very rusted and has spots that have completely rusted through the Vent Pipe. Flue Pipe is metal has become weak and is easily broken when pressure is applied. Taped sections of pipe where there was visible damage to seal. Reviewed with homeowner and provided estimate for the Replacement of the Flue Pipe. The office wil
Performed Precision AC tune up on 3 Indoor Mini Split Units and 1 Outdoor Mini Split unit. Cleaned a Filters and Indoor Coils. Checked Electrical Connections at Indoor and Outdoor Units. Checked Flare Fitting Connections at Outdoor Unit to ensure there were no leaks. Put each unit in operation and measured Return and Supply air temperature readings. All units cooling with a 18-20 Degree Temperature Split. System operating to standards at this time.
Performed Heating Tune Up on Gas Boiler. Removed and Cleaned Burners. Cleaned Pilot Assembly. Removed Flue Pipe at Boiler and cleaned out debris and rust that was collecting inside the exhaust. Put the 1st Floor and Second Floor Zones in Operation. Performed Combustion Analysis on Boiler. Monitored Water Temperature and Pressure on System. Water Pressure was maintaining 18 PSI, and Boiler was cycling off at 180 Degrees. The Flue Pipe is starting to corrode and rust is forming along the inside and and outside of the Pipe. Recommend replacement of the Flue Pipe. Performed Heating Tune Up on the Mini Split System with 3 Indoor Units. Cleaned All Air Filters on Units. Inspected and Cleaned Indoor Coil. Inspected Electrical Components on the Indoor and Outdoor Units. Put system in Heating Mode and tested Supply/Return Air Temperatures.
Performed Precision AC Tune Up on Daikin Mini Split System with 1 Outdoor Unit and 3 Indoor Units. Cleaned All Filters and Inspected Blower Wheels and Indoor Coils. Inspected Electrical Connections on Indoor and Outdoor Units. Inspected Refrigerant Pipe Connections at the Outdoor Unit to ensure they were sealed. Put each Indoor Unit into operation and measured Supply and Return Air Temperatures. System is operating to standards at this time.
Performed Precision Heating Tune Up on the Gas Fired Boiler. Removed Burners and Cleaned. Cleaned Pilot Assembly and Thermocouple. Inspected Heat Exchanger while Burners were removed. Cleaned Pressure Switch Tubing. Put Boiler in operation to test. Tested the Expansion Tank and found that it was full of Water. Recommend Draining Expansion Tank of Water. The Expansion Tank helps protect the Boiler and the Piping in the event of an influx or increase in Water Pressure. Included an estimate for the Draining of the Expansion Tank. Tested Water Temperature and Water Pressure. Performed Combustion Analysis on Boiler. Performed Heating Tune Ups on the Mini Split system with Three Indoor Units. Removed and cleaned Air Filters and Indoor Coils on each unit. Tested operation of Units in Heating Mode. Inspected Components on Outdoor Unit and tested for proper operation. Supply/Return Air Temperatures on each system were to standards. Showed Homeowner how to remove the Air Filters on the Units t
Service call that the Gas Fired Boiler was not operating. Arrived onsite and spoke with Homeowner about issue. Found that the Pilot was lit but the Boiler would not Fire off. After troubleshooting system, found that the Pressure Switch was not gettng the correct amount of pressure to close and open the Gas Valve. After further troubleshooting determined that the Flue Pipe was clogged. Removed Flue Pipe and found a Birds nest in the Vent Pipe. Cleaned Vent Pipe and reassembled. Resealed the Vent Pipe with High Heat Silicone and Metal Tape. Put Boiler in operation and performed Combustion Analysis. The office will call to schedule a return visit to perform Heating Tune Up on Mini Split System and the Gas Boiler.