Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed ac tune up on three unit two in the basement and one on second floor, replaced filter, flushed drain check supply and rerun temp, motors, noticed code pump for first floor Lennox system has old pump and is taking some time to discharge also vinyl goes to the outside and is in bad shape, would recommended replacement of pump and run new viny to sink, for both units in the basement supply temp is 50 return air 66 only 16 degree split, refrigerant pressures ok good super heat and sub cooling on second floor heat pump found unit to be low on refrigerant only 10 degree split 66/56 indoor coil is in bad shape leaking refrigerant, also condensation pump is sitting on top of drywall would recommended replacing pump with shallow pump style and make necessary repairs on new drain if canâ€™t be installed inside unit pan we can make metal pan for pump and installed float switch as well, recommended replacing heat pump system
Recently installed humidifier by us, was leaking water, check humidifier operation and found drain line restricted by kink on vinyl tubing, made necessary repairs, add 3/4 pvc fitting and some tubing to bring up drain and eliminate kink on vinyl tubing, test humidifier for couple minutes draining ok test pump ok no charge under installation warranty
Performed 3 heat tune ups and installed a Aprilaire 600M humidifier. Adapted condensate drain for humidifier. Installed 2 Honeywell t10 thermostats and set up sensor.