Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Went downstairs in basement to system which is a propane gas furnace with a/c. Propane furnace is a 1996. Gave thermostat a call for heating and found inducer motor running, proving pressure switch but no hot surface igniter. Ohmed out hsi and found it only reading 3 ohms. ( this is the Honeywell smart valve set up). Took off burner panel and found heat exchanger in bad shape. Took off evaporator coil panel and found rivets have separated at clam style heat exchanger. When the rivets pop out heat exchanger can open up while metal is heated it can cause exahaust gases to escape into air duct. Recommended replacement of gas furnace and a/c . Set up appointment with office to have a comfort consultant come out and give a price on replacement. Shut off gas and power to system .