Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed precision heat tune up on amana heat pump system. Replaced Aprilaire 313 air filter ( homeowner provided). Checked all electrical conections and components. Found high and low pressure switch wires rubbed at outdoor heat pump tapped up and moved away from piping. Also found high voltage wiring at indoor unit was a little loose at single pint entry and wire had melted some cut off melteted end and made sure electrical conection was secured. Heat pump was locked out on a code 3 from dirty air filter. Homeowner will replace more often. Checked refrigerant pressures and temperatures at indoor and outdoor units. Heat pump is working fine at time of inspection.