Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Performed Quality Assurance on 2 Amana Heat Pump/Air Handler systems. Reviewed installations with homeowner. Checked the Air Flow noise issue for the Second Floor System. Unit is a 2-Ton system and has 3- 6â€ Runs on it. The Register in the Master Bedroom has a lot of noise coming from it. No Dampers are present on the Ducts for the Second Floor. Lowered the Airflow Trim by 10% on the system. Dan is going to perform Duct Work Calculations, and assess the Heat Kits/Panel Sizing and review with Joe before following up the customer.