Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Pressures when I started system: 45 LO 150HI with 57 SH .3 SC. Charged system 3 pounds 3 oz. RS44B while monitoring for Target subcooling 10Â°. Final Subcool 9.7Â° Final Superheat 17.2Â°. TD 16.2Â°F with 62.8Â°F supply temp and 56% Relative humidity at return.. Except I n the event of a very serious leak, system will perform at design conditions until the time of install 7/15/21. Cleaned trap at condensate. Added condensate tabs. Tested pump.