Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Found first floor a/c system locked out on a 04 code at outdoor unit. ( locked roter code). When this issue occurs the compressor is not starting fast enough and the board locks out the outdoor unit. Installed a ks1 hard start kit to assist the compressor on start up. Checked 410 a pressures at 86 degrees. Pressures were 299/124 with 9.6 degrees subcooling. Also turned on dehumidification in cool cloud. Also added inline drain kit for intake pipe. A/c system is working fine at time of service.