Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, and Amana condenser. Brazed in line set with nitrogen. Connected high volt and low volt connections and sealed holes. Installed new Amana gas furnace and evaporator coil and brazed in line set with nitrogen. Pressure tested to 300 and evacuated down to 115 microns. Installed new return , plenum, and sealed all connections. Installed new switch and receptacle and wired in high volt. Installed new ez trap and condensate pump and wired safetyâ€™s to break r. Reconnected gas line and leak checked. Installed new vinyl to discharge. Reconnected venting. Reinstalled existing humidifier. Tested system in heat and adjusted gas pressures and performed combustion test. Tested system in cool and adjusted refrigerant charge. Tested condensate pump. System working great at time of install.